ISDS 



* Well regulations require that wells be installed a minimum of 15 feet from the property line. 



(1) 100 feet is a minimum acceptable distance and no variance shall be granted for a lesser distance except 

 with priw written approval of the Dept. of Environmental Quality Engineering. 



(2) All distances shall be measured from the average of the mean annual flood elevation in inland areas and 

 from Mean High Water in coastal areas. 



(3) 10 feet if constructed of durable corrosion resistant material with watertight joints, or 50 feet if any 

 other type of pope is used. 



(4) It is suggested that the disposal facilities be installed at least 10 feet from, and 18 inches below water 

 supply lines. Wherever sewer lines must cross water supply lines, both pipes shall be constructed of class 

 150 pressure pipe and should be pressure tested to assure watenightness. 



(5) The applicant should be aware of his obligation to comply with the requirements of the Wetlands 

 Protection Act, G.L.. C. 131, SS 40. 



94 



