J 34 



The Weekly Florists^ Review. 



Dkikmhki: 11. laiij 



WHEN IN NEED OF 



BOXES 



Try our improved folding box, v\ith super- 

 ior white finish and improved corner lock. 



I^'Samples free on application. No 

 charge for printing in 500 lots or over. 



C. C. POLLWORTH CO., Milwaukee, Wis. 



Mr'ntlon Thp Review when you write. 



HOT WATER CIRCULATION. 



1 liavc! two housos 18x100, each lieated 

 with two oveilicad -i-iiu-h pipes, each of 

 which go \inder a hciich into thieo 4iiicli 

 cast iron pipes. 'Hie ciiciilation is ex- 

 ceeding-ly slow all around, under one 

 bench particularly the cast iron pipes 

 <to not warm up and in hard firing only 

 to the center of the hovise. the other half 

 reniaininf; cold. Under the other l>enches 

 the east iron ])ipes get warm, but not 

 to the degree they should. The overhead 

 ]>ipes are very ,varm. 



Can you suggest a reason and a rem- 

 edy for the pipes vinder the bencli re- 

 maining cold half way? In general I 

 think the three 4-incli east iron pipes 

 on each 2-inch flow are too much to re- 

 turn, yet only under one hench (on north 

 side, too) do they icmain cold half way. 



KXQt'IItF.I!. 



Tlie trouble to which Enquirer refers 

 may be due to several causes, the most 

 probable being the fact that a 2-inch 

 main, 100 feet long, is too small to sat- 

 isfactorily feed 300 lineal feet of 4-inch 

 cast iron pipes for returns, and also the 

 want of sufficient direct vertical fall from 

 the return main back to tnc boiler. 



I cannot advise definitely as to the 

 best method of overcoming the troubles 

 without more detail as to grades of 

 pipes, depth of Iwiler below coils, size 

 or capacity of boiler, size of mains from 

 and to the boiler and arrangement of 

 expansion tank and air vents. 



ITexry W. fiiniioxs. 



New Yoik. 



PIPING. 



Will six lines of 2-incli steam pipe heat 

 a house 24x84, side walls 3 ft. and 7 ft. 

 to peak? Xo glass in side walls. Pipes 

 are on sides and overhead. Feed pipes 

 are on each side, about 8 ft. apart, and 

 returns are two lines on each line of side 

 posts. Boiler is in end of house and 

 get some heat from it. Outside terajier- 

 ature sometimes drops to 10 to 15 de- 

 grees below zero. I wish to maintain 

 oO to 00 degrees in the liouse. 



J. H. IT. 



With the six lines of 2ineh pipes full 

 of steam at 4 or 5 U)S. pressure he can 

 maintain 50 degrees in the greenhouse 

 in the coldest weather. Two-incii jiipcs 

 are not desiraWe for steam circulation. 

 It would be better to use a larger num- 

 ber of pipes of smaller diameter for the 

 coils. Hf-xry W. GinBoxs. 



-New York 



KRAMER'S 



POT 



HANGERS. 



Neatest, slniplest. 

 ni OB t convenient 

 aod only practical 

 device forconverl- 

 Ing ordinary flower 

 potB Into banging 

 baeketB. They fit 

 all standard made 

 pots from 2 to 10 

 Inches In diameter. 

 The Illustration 

 shows how they 

 are attached. Just 

 the thing- lor 

 hanging up Ferns, 

 Begonias, etc. You 

 can make room and 

 money by their 

 use. Try them. 



Price with wire 

 chain as shown in 

 cut 91.00 per dozen 

 by express. Sam pie 

 dozen by mall 11.25. 



I. N. Kramer&Son 

 Cedar Rapidi. Ii. 



Mention The Review when you write. 



C 



ut Flower Boxes 



WATERPROOF Corner Lock Stjle. 



The best, stroneeal and neatest folding 

 cut flower box ever made. Cheap, durable, 

 handy. To try them once la to use them alwaj-s. 



DON'T USE OLD STORE BOXES. 



If you have any doubt, send for samples, which 

 speak for themselves. 



Size No. I.....';x4^.Yl6..(l.;operl00; 115.00 per 1000 

 ■■ No. 2....3xexlS.... 2.00 ■■ 18.00 



•■ No. 3 ...4X8X18.... 2.40 '■ 22.00 



■ No. 4.... 3x6x20.... 2.75 " 25.00 



•■ No.5... .4X8X22.... 3.00 " 28.00 



No. c. 



1nSx2s. 



S.VOO 



The Livingston Seed Co., Columbus, 0. 



Box 104. 



Mention The Review when you write. 



Ise DINNITE 



According to direcilonB. and cease 

 suffering from Black Spot or Insects 



on any of your Rose Plants. 

 Write for prices and further particulars to 



DUNNE & CO., "VIw^^^^B^^: 



Mention The Review when you write. 



THADEN'S WIRE TENDRIL 



TESTZMOKIALS. 



From A. Gude& Bro.. Wash- 

 ington. D. C. April 11. Ht02. "In 

 reply to your Inquiry of March 

 m in reference to the Wire 

 Tendril, we beg to say that we 

 find them very satisfactory In 

 every respect. 



AWARDED 



CERTIFICATE OF MERIT 



at tile 



isherllle ronvenllon of (be 

 S. A. F. and O. H. 



Sample package of 100. by 

 mall prepaid, 60 cents. 



H. THADEN & CO. 



472 W. Hunter St., ATLANTA, GA. 



w 



HEN YOU WANT 



Engravings made 



send us Photos or clipplntrs from other 

 catalogues and let us reproduce them. We 

 make the cuts for the Florists' Review. 



DEARBORN ENGRAVING CO., 



300-306 Dearborn St., CHICAQO. 



Holds Class 

 Firmly 



See the Point »" 

 FEERLCSS 



Olazlnc Points u-e Uiebeat. 

 No righu or lefts. Box of 

 1,000 poloU 75 oU. poitpkld. 



HENKT A.DREER, 



714 ChMlBBt St.,Pkllk,l>k. 



THE E. G. HILL CO. 



Wholesale 

 Florists, 



RICHMOND, INDIANA. 



WALTER MOTT 

 SEED & BULB CO., 

 Jamestown, N. Y. 



SEND FOB CATAIiOOUE. 



HITCHINGS & CO. 



233 MERCER ST., NEWYORK. 



GREENHOUSE BlILDERS 



Hot Water Boilers, Pipes, Fittings 



Send Four Cents (or Catalogue. And Vpniilating Apparatus 



I 



