Jordan's Patent Wrought Iron Water Hea'er. 



A NEW PRINCIPLE. 



The boilers :ue constructed of horizontal pipes of the same inside diameter as those that form 

 the heating pipes, thereby producing a very rapid circulation of the water. 



LENGTH SEVKN FEET. DESCRIPTION. 



No. 1 shows a side view of one-half section, with U steam 

 propeller. Also shows sections of chimney, ash-pit, and brick 

 arch around the boiler, with downward draft to chimney. 



No. 2 shows end view, with rear end closed with pipes ; ash- 

 pit below and brick arch above. 



No. 3 shows boiler before it is set in the brick, with a few 

 pipes broken away, to show the steam generator. 



The improvements claimed are : a larger heating surface, 

 as compared to the amount of water in the boiler ; a more 

 rapid circulation of water by the use of steam generator to 

 move the water ; a larger fire-hole, so that soft coal can be 

 used and not obstruct the draft; and cheapness. 



Extracts from the Patent, No. 173,300, Dated 

 February 8th, 1876. 



By making the pipes throughout the whole lengtli of the 

 boiler and heater of the same interior diameter there is an 

 even flow through the pipe at all parts, and no shoulders in 

 the pipe to cause any check to the flow. 



It is obvious that the boiler-pipes being exactly the same 

 interior size as the radiator and connecting-pipes, a new and 

 quite valuable result is obtained, as the simultaneous move- 

 ment of the water is insured through the whole series of 

 pipes at the same speed, thus preventing any eddy and dead 

 water. 



The U-formed steam water propeller, by descending into 

 the furnace and entering the water-pipe at an inclinntion, 

 causes a circulation in the w'ater-pipes almost immediately 

 the fire is lighted, and before the water has time to become 

 heated in the water-pipes. The end bends of the water-pipes, which close partially the back of the 

 fire-space, receive the full blast of the products of consumption. 



TIIUTHS TO BE CONSIDERED. 



If water moves rapidly into and out of the furnace it must carry olf the heat rapidly into the 

 room to be heated, thereby saving the fuel. The front is of iron and can be easily removed to 

 clean out du.st, <fec. 



SETTING THE BOILER. 



Build foundation wall 12 inches wide, so the pipes will set about I} inches inside the walls, and 

 3 inches above the grate bars; let the boiler rest on one fire brick at front and one at rear. Let 

 the rear bridge wall for the grate bars he heavy and raise above the grate bars about 10 inches to 

 one foot, and of fire brick. The Chimney should be started from the bottom of the furnace, and 

 be at least 25 feet high, and an opening at least one foot sqare. 



PRICE OP "BOIIiERS (of wrouoht iron, with iron front and grate bars.) 



Small boilers without prate bars or iron iront ... {25 to $nO each. I No. 4 to heat 1900 to 2000 feet of pipe... „ $175.00 each 



No. 1 to heat 500 to 750 leet of pipe $75 00 " | " 5 " " 2000 " 300O 225.00 " 



" 2 " 750 " lOnO " " '• 100.00 '• I " 6 " " 3000 " 5000 " " " 300.00 " 



" 3 " 1000 " 1500 " " " 125.00 " | Valves for 4 inch pipe 10.00 " 



Large boilers made to order. Where no iron front or grate bars are wanted, 10 per cent, de- 

 ducted. 



Water-pipe and all kinds of fittings at present 30 per cent, off the card prices. 



Men furnished to put up the furnace and contracts taken to heat any building, and can be placed 

 where hot air furnace has been used. 



We have had seventeen years experience in handling water heaters, and can guarantee our work. 



JORDAN & BRO., 



niav.:2 612 Olive Street, St. Louis, Mo. 



