314 The Country House 



by heavy sheet-lead flashings 18" square, with a funnel around the pipe. The flashing is to be 

 securely fastened to the roof, and the funnel is to be turned over and caulked into the hub of the 

 iron pipe. 



Protect the open ends of all soil, waste and vent pipes above the roof with strong wire baskets 

 properly secured. 



Traps. Trap all fixtures in the building, unless otherwise specified, and half S or running 

 traps of the same size and material as the wastes from such fixtures. All traps are to be venti- 

 lated as specified and are to have brass trap screws. 



Hose Connection. Run a \" galvanised-iron pipe to the two front sides of house, with a hose 

 bibb (N. P.) placed at the end of each, and a lever-handled stop and waste shut-off inside the 

 cellar wall. [N. P. means nickel plated.] 



'I link. Furnish and set in roof, directly over main stairway, a tank 6' o" x 3' o" and 2' o" 

 high. Line with 14 oz. copper, tinned. 



Connect a lead-lined iron overflow pipe 3" from the top of the tank, and run to the gutter 

 outside with a bra>- Hap valve on end. 



Run a i\" lead-lined iron pipe from the bottom of the tank to the overflow pipe, with an 

 open-way valve close to tank. 



Supply the tank with water through a i \" lead-lined iron rising main from the sill under the 

 main stairway. No cold-water branches to fixtures are to be taken from this riser. Place a ball 

 cock on this supply to prevent overflow. 



Provide and place at the bottom of the tank a tank valve, with an air tube tarried above the 

 water level in the tank, and from it run a |" lead-lined iron pipe to supply the boiler and ri.xture-. 



Water Supplies. The Owner will bring the water to the hou-e, where the plumber will make 

 proper connections with the house system. [This gives a chance for the ( hvner to install such 

 system of water supply as the case may demand.] 



Run the necessary branches as required and specified. Place a lever-handled shut-off on 

 the main supply just inside the cellar wall. All -upplie- are to be graded so they will drain dry. 

 All hot and cold water lines are to be placed at lea.-t i" apart. No MX k i- to be placet! at the' end 

 of a line pipe, but the pipe must extend beyond vertically a sufficient length to form a proper air 

 chamber. 



Boiler. Furnish and set complete where shown on drawings one 4o-gallon Badger Bros, 

 copper boiler set on galvanised-iron stand. 



Supply the boiler through a }* brass pipe where exposed in kitchen, with a lever-handled -hut- 

 off or valve placed near the boiler. 



Connect the boiler with the waterback of the range with \" brass pipes and brass couplings. 

 The boiler is to have a sediment pipe and cock. 



Supply a \" brass safety pipe, to be connected at the top and to extend upward in such course 

 as may be directed to a height above that of the supply tank in the attic. At this point it is to turn 

 down over the tank, so that any <li-i -barge may be taken care of. 



Kill lien Sinks. Furnish and set complete in kitchen, where shown, one 24" x 40" soap- 

 stone sink, with 12* back and soap cup, 5" brass strainer and coupling. 



Supply the sink with hot and cold water. Cold-water supply to be \" lead-lined iron pipe; 

 hot-water supply to be J" brass. Both to have brass compre.-.-ion cocks. The cold-water cork 

 to have a hose end. 



Waste through a i^" lead branch waste connected to the soil. Fit with 5" jug trap with 

 brass trap screw. 



Water Closet. Furnish and set in bathroom one F. \Y. Webb Mfg. Co. "Lucania" water 

 closet, 55-B, with style H seat, chain pull, dark-cherry seat and tank. 



Furnish and set complete in basement, where shown, one cast-iron porcelain-lined short 

 hopper, with cistern 18" x 10" x 10" on brackets. 



Fit with N. P. chain and hardwood pull and hardwood seat and lid, i" lead flush pipe. 

 Connect closet to soil with a 4" lead branch. 



II ash Trays. Furnish and set in laundry, where shown, a three-part soapstone wash tray, 

 with soap cups. Provide with polished-bra.-.- chain> and plugs and rubber .-topper-. 



Supply each part with hot and cold water, cold water through \" lead-lined iron pipe and 



