580 



ELECTRICAL EQUIPMENT 



by a disconnecting switch hook. There is not needed the room 

 which would otherwise have been necessary for the operator to 

 use the switch hook at the considerable angle required. 



FIG. 372. 110,000-volt Disconnecting Switch with Safety Catch and Opening 



Device. 



The insulators, insulator caps, and terminals are standard. 

 The blade is a copper rod with a cast eye fastened on one end and 

 a readily renewable solid brass contact tip on the other. The sta- 



