rsa 



.SCIENTIFIC AGRICULTURE 



Mai( 



v.yjt 



Complete Power Equipment From 



Liquidating Mill 



Must Sell Quick Immediate Delivery 



You'll Find Real Bargains Listed Below 



bOILERS 



CG 431 T. — Three 20S H.P. Smith HKT boilers, 78" in 

 diameter x 16'. 150 lbs. pressure. 150 tubes 3" x 16'. 

 2.000 sq. ft. heating surface, 52 sq. ft. grate surface. %" 

 shell, 9-16" heads, longitudinal seam double butt strapped, 

 quadruple riveted, girth seam single riveted. Complete 

 with Coe's shaking grates, Vulcan soot blowers. Burrows 

 automatic water regulator, horizontal return stop and 

 check valve and catalog fittings. Two boilers are equip- 

 ped with Foster superheaters for 125° super heat. Hart- 

 ford insurance for 155 lbs. pressure 1920 inspection. Very 

 good condition. 



CG 431 v. — One 200 H.P. B. & W. Sterling water tube 

 l)Oiler 10' X 15' 11" x 18' 7" high; 3 steam drums, 36" 

 diameter x 10' 3- %" long, of %" steel; steam drum tube 

 sheet %" thick; 160 lbs working pressure, lap joint con- 

 struction. 42" mud drum with 7-16" shell, and 11-16" 

 tube sheet. SVt" tubes. Heating surface 2,000 sq. ft., 

 grate surface 56.25 sq. ft. Complete with Foster super- 

 lieaters for 125° super heat. Diamond soot blowers, Coe's 

 .lutomatic feed water regulator and low water line, Coe's 

 sliaking grates, catalog fittings. Excellent condition. 



CG 431 V, — One 218 H.P. Dillon HRT boiler, 78" dia. x 

 2(1' long, flush ends, flush front, single setting. I-beam 

 suspension, 114-3i^" tubes, 20' long, 2,200 sq. ft. heatmg 

 surface. 49 sq. ft. grate surface, shell 19-32" thick, heads 

 %" thick, double butt strap, quadruple riveted. 156 lbs. 

 pressure, A.S.M.E. code. Complete with Coe's shaking 

 grates, Vulcan soot blowers, Burrows Automatic water 

 regulator. Excellent condition. 



BAROMETRIC CONDENSER 



CG 431 Z. — One 14" Buckley Barometric condenser, 14" 

 steam inlet, 5" water supply and tail pipe fitted with 10 ' 

 atmospheric relief. Floor space 3' x 3'. overall height 15'. 

 (_iood condition. 



ENGINES 



CG 431 K. — One 125 HP. Chandler & Taylor horizontal 

 steam engine, size 14" x 18". 140 R.P.M.. Tangye frame, 

 left hand slide valve, flywheel, 16" dia. x 16" face, iVi" 

 steam, 6" exhaust, Gardner governor, Nathan lubricator, 

 oil cups and throttle valves. Floor space S' 6" x 12'. 

 Numerous spare parts. Fair condition. 



CG 431 D. — One 140 H. P. De LaVergne oil engine, Type 

 D 245, Specification P, Cylinder 20" diam. x 34" stroke. 

 164 R.P.M., flywheel 138" dia. x 15" face. Weighing 13 

 tons. Machine is provided with air compressor for oil 

 feed but no pressure tank for starter. Numerous spare 

 parts. 



CG 431 Ii. — One 150 H.P. Ames horizontal automatic 

 steam engine, 16" x 18", 225 R.P.M., with SO lbs. initial 

 steam pressure and 5 lbs. back pressure, side crank, fly- 

 wheel governor. Flywheel 70" x 16" face, weighing 3,600 

 lbs. Complete with throttle valves, cylinder lubricator, and 

 gravity oiling system for bearings, vertical steam separ- 

 ator, etc. 



CG 431 M. — One 125 H.P. Chandler & Taylor horizontal 

 steam engine 14" x 18" Tangye frame, left hand, side 

 crank, slide valve with Gardner governor, 4J4" steam inlet, 

 6" exhaust, floor space 9' x 12'. Numerous spare parts 

 included. 



CG 431 N. — One 250 H.P. Improved Green automatic hor- 

 izontal steam engine, 20" x 42" with double ported slide 

 valves, left hand, detached girder frame, 106 R.P.M. with 

 90 lbs. initial steam pressure. 7" steam inlet, 9" exhaust, 

 operating noncondensing, exhausting at atmospheric pres- 

 sure. Split flywheel 12' diam. x 30" face. Complete with 

 throttle valve, steam separator, sight feed lubricator and 

 oil cups. Numerous spare parts included. Fair condition. 



CG 431 O. — One 300 H.P. Kerr mixed pressure turbine, 

 size F. 5, speed 2,200 R.P.M. 4" high pressure, 8" low 

 pressure steam inlets, 16" exhaust; 4-1 herring bone speed 

 reducing gear, connected by flexible coupling to rotor 



shaft: belt pulley 20" diam. x 31" face. Provided Willi 

 force feed lubricating system. Numerous spare parts in- 

 cluded. 



GG 431 P.— One 10 H.P. Donnegan & Swift Metropolitan 

 horizontal steam engine, 7" x 8". side crank self contained 

 Flywheel 34" x S", belt wheel 38" x 6", IVa" steam, 2" 

 exhaust. Complete with Gardner governor, throttle valve, 

 one pint Nathan lubricator. Good condition. 



CG 431 Q — One 5" x 6" Sturtevant vertical steam en- 

 gine, self contained, center crank, governor wheel 30" 

 diam. x 6" face, belt wheel 30" diam. x 6" face, 1" steam 

 IVi" exhaust. Complete with one pint cylinder lubricator 

 and oil cups. 



CG 431 B. — One 5% x6" Greenfield, vertical steam en- 

 gine, self contained, center crank, flywheel governor, fly- 

 wheel 2 1" diam. x 5" face, 1" steam, 1^" exhaust, one 

 pint cylinder lubricator ant oil cups. 



CG 431 S. — One 5" x 6" Donnegan & Swift Acme vertical 

 steam engine, 1" steam inlet, I'/t" exhaust, self contained 

 side crank, flywheel 24" diam. x 5" face. One pint cylin- 

 der lubricator and oil cups. 



ENGINE GENERATOR SETS 



CG 431 X — One 7 KW General Electric Marine type en- 

 gine generator set. 5" x 4%" vertical steam engine, direct 

 connected to type MP Class 6-7-550 Form C, 110 volt DC. 

 generator, 64 amps., engine rated at 10 H.P.. Complete 

 with switchboard. Very good condition. 

 CG 431 Y — One 10 KW Westinghouse 125 volt D.C. engine 

 generator set SO amps., 825 K.P.M., frame type S No. 5, 

 belt pulley 12Vi" diam. x 8" face. Complete with slide 

 rails and pulley and switchboard, including field rheostat. 

 Driven by 7" x 8" Vim horiz. automatic steam engine. 

 Size No. 3. Center crank, 2 flywheels, 34" diam: x 9" face, 

 flywheel governor, steam separator. Good condition. 



FEED WATER HEATER 



CG 431 "W. — One 2,500 H.P. Cochrane open type feeil 

 water heater, 9' 5" x 4' 0" x 8' 3" high, with recording 

 meter: cast iron shell with 20 trays 28" long x 12" wide, 

 arranged in 4 rows equipped with "V "notch Weir, and 

 single clock driven recorder, with integrator and a flow in- 

 dicator; capacity of Weir 90,000 lbs. per hour. Equipped 

 with Cochrane baffle plate type oil separator. Excellent 

 condition. 



GENERATOR 



CG 431 J. — One 20 KW Western Electric generator Type 

 ML, 115 to 125 volts DC, 1,200 R.P.M., 160 amps.; Com- 

 pound wound; Belt pulley 8" diara. x 7" face. Complete 

 with switchboard, circuit breaker and field rheostat. Ex- 

 cellent condition. 



SMOKE STACKS 



CG 431 A — One 54" x 100' Guyed steel stack; 55' of 

 5-16" and 45' of %" steel resting on cast iron bed plate. 

 Fitted with 2 Guy bands. Good condition. 



CG 431 B. — One 48" x 95' Guyed steel stack Vt" thick, 

 resting on cast iron bed plate, 2 Guy bands. Good con- 

 ^tition. 



CG 431 C One 54" x SO' Guyed steel stack %" thick, 



resting on top of short brick stack. 2 Guy bands. Good 

 condition. 



WATER WHEELS 



CG 431 H One 37 H.P.vertical water wheel, built bv S. 



Morgan Smith Co., York, Pa.; size 27", left hand, 150 

 R.P.M., with 8' 2" head. Set in open wheel pit. Fair 

 condition. 



CG 431 I. — One 78 H.P. vertical water wheel, built by S. 

 Morgan Smith Co., York, Pa.; size 39", right hand, 150 

 R.P.M., with 8' 2" head. Set in open wheel pit. Fair con- 

 dition. 



Write or Wire for Full Details and Prices 



TECHNICAL PRODUCTS COMPANY 



INCORPORATED 



CHICAGO 591 Fifth Avenue, NEW YORK TORONTO 



