March 15, 1917. 



The Florists' Review 



93 



Mention The B-vlew when you write. 



PIPE 



Wrought Iron of sound second-hand Quality 

 with new threads and coupling, le-ft. lengths 

 and up. Also pipe cut to sketch. We guarantee 

 •ntire satisfaction or return money. 

 Established 1902. 



rrAFF & KENDALL, Fiudrr St. Newark, N. J. 



M^Bttea Ttw BsTfw wh<n yp« writs. 



Full Weight Wrought Iron 

 and Spollorlzod Stool Plpo 



Ciib, Bends, Railings, etc, nade to Sitclcli 



FORD & KENDIG CO. 



97 Kortb 7th Sti«et 



S4th and "Wood Streets 



Mestl— Tbs IUtIsw whts yos write. 



PHILAiyELrHIA 



Pipe and Tubes 



*U tIZEt CUT TO IKETCH 



Philadelphia Second Hand Pipe Supply 



1003' N. 7di St, PHILADELPHIA, PA, 

 lisntloa Ths Bsrlsw whsn yon writ*. 



grate surface 32x60 inches, be large 

 enough to heat the houses to 60 degrees 

 in zero weather? How should the pip- 

 ing be arranged! I have a lot of sec- 

 ondhand pipes, in 4-inch, 2-inch andl^/^- 

 inch sizes. Would you advise me to use 

 these? The cellar is about seven feet 

 below the greenhouse flo( rs. 



J. M.— N. Y. 



The heating capacity of hot water 

 boilers varies with the character of the 

 fire surface, as well as with the area 

 of the grate. To heat the two houses 

 described, a boiler with a rating of 

 4,000 square feet will be required. We 

 judge that the boiler with a grate 32x60 

 inches will handle at least 3,500 square 

 feet of radiating surface with ease, and 

 if that is the case it will probably an- 

 swer for the range in question by giv- 

 ing the fire a little extra attention in 

 severe weather. 



Since the amount on hand of each 

 kind of pipes is not stated, we cannot 

 give any really definite advice as to 

 how these can be used to the best ad- 



IMICO 



Hot Water Boilers 



Made by 



Illinois Malleable Iron Co. 



1801-1825 Diversey Boulevard 



CHICAGO 



Are noted for COAL ECONOMY and 

 good results generally. 



SEND FOR CATALOGUE 



iiiiiiiiiiiiiiiiiiiiiiiiiniiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiiig 



i SZ: BacktoBofe H> j7*^ ^ t^ y = 



i SYSXE^M Economy of r uel I 



5 PWiEGIN NOW to find out about the "Morehead" System. Send right away E 



S I PJ for the "Morehead" book for florists. In it you will find an easily under- — 



= I BTl stood discussion of the boiler and condensation question from the prao- s 



= LSM tloal standpoint of the Grower of Flowers. Write for this help TODAY. s 



= MOREHEAD MFG. CO. 



Dept. "M" 



299 



DETROIT. MICH. = 



nllllllllilllllllllllllllllllllllllllllllllllllllllllllllllllllllllllllimillllllllllllllllllllllHIIHIB 



Mention TtM Burlaw wfcen yau write. 



STEEL 



BKTTTRM 

 TUBULAR 



BOILERS 



Johnston HoatIng Co. 



ISl ■. 2MII Slra«t mw YORK 



Mention The RcTlew when yon write. 



vantage. The 2-inch pipe may be used 

 for the returns in both of the houses, 

 but we would not care to use the 1%- 

 inch pipe in the 160-foot house, al- 

 though it would answer for the shorter 

 house. Our choice would be to run five 

 2iA-inch pipes as flows, but the 4-incii 

 may be substituted on the wall plates. 

 We would prefer, however, to dispose 



New 

 Wrought Pipe 



Black or Galvanized 

 Delivered Anywhere 



Send us a list of your needs. We 

 can save you money. 



King Construction Co. 



North ToDawanda, Naw Yoik 



of the 4-inch pipe and use a smaller 

 size. 



