.CV-. '' ,; 



NOVBMBER 9, 1916. 



The Florists^ Review 



89 



If you need a boOer in a hurry, telephone or telegraph at our expense 



The 

 Kroeschell 



Is the most efficient boiler built. 



Has the longest fire travel. 



Has thin waterways. 



Has water front, back, sides 

 and top. 



Made of boiler plate, not cast 

 iron. 



KROESCHELL BROS. CO., 444 W. Erie Street, CHICAGO 



Mention The Review when yon write. 



^^Superior'' 



INTERNAL-FIRED 

 BOILER 



For Hot Wator Hoating 



Superior Machine & Boiler Works 



840.850 W. Suporior Stroot 

 CHICAQO 



. M^wtloB 'n^ R»t1»w whrB yon write. 



''fr and size of them, to heat .1 green- 

 liouse 25x100. The temperature wanted 

 is 60 to 70 degrees. On rare occasions 

 'he outside temperature drops to 1.5 de- 

 ;,nees below zero. H. M.— 111. 



We are not able to determine from 

 ^lie letter whether steam or hot water 

 's to be used. Neither are we informed 

 •is to the amount of glass in the walls, 

 if any. 



For hot water, in a house with wood- 

 '^11 walls not more than four feet high, 

 We would use three 2,i^-inch flow pipes 

 <'i"d sixteen 2-inch returns. One flow 

 should be placed upon each of the side- 

 ^[sll plates, each to feed five returns, 

 "ither on the walls or under the side 

 henehes. The other flow should be 

 placed two*or three feet below the ridge, 



IMICO 



Hot Water Boilers 



Made by 



BDnois Malleable Iron Ca 



18ei'1825 Diversey B«alevard 



CHICAQO 



ll«tMl for coal •conoiny and 

 rasuits sanarally 



SEND FOR CATALOaU# 



Mention Th^ R«v1«w when yon write. 



HIGHEST PRICED and CHEAPEST 



BOHJERS aiABK 



GiBLiN Greenhouse Boilers 



6IBUN 



109BromdSt., 



at CO. 



Utica, N. Y. 



LET US TELL YOU 

 ABOUT THEM 



Mention The ReTiew when yon write. 



^ 



3lC 



% 



BOILER FLUES 



We make a specialty of handling 

 carefully selected Boiler Flues, 4-in. 

 diameter and other sizes, for g^reen- 

 housepipinK,Gutter Posts, etc. Also, 

 we make a specialty of flues for 

 retubingr boUers. All flues are 

 thorouirhly cleaned inside and out, 

 trimmed, and are ready for use. 

 General Sales Aeents for Stuttle's 

 Patent Clamp and Elbow for joining 

 flues— no ipacking, no leaks. New 

 standard pipe and all kinds of green- 

 house fittings. Right prices and 

 prompt shipment. 



H.t M U NSON 



Est. 1898 Phone Superior 672 

 1353 N. Clark St. Chicago 



^ 







Mention The Reylew when 70a write. 



and the remaining six returns should be 

 connected with it at the farther end of 

 the house. If there is glass in the 

 walls, an additional return will be re- 

 quired for each two feet of glass. Run 

 all pipes with a slope of one inch in 

 ten feet and connect the expansion tank 



Gorman's 



Special Greenhouse 



Steam-Air Vent 



Stops"Air-inri>e"TroBbles 



Will positively take air 

 out of heating plants and 

 will keep your coils hot. 

 No waste or blowing of 

 steam. 



Valves in use for twelve 

 years now good as when 

 put in. 



J. F. GORMAN 



250 W. IZath St.. NEW YORK 



Mention Tfce B«t1»w whea yon write. 



with the highest point of each flow 

 pipe. 



To heat the house with steam, use a 

 2Vj-inch overhead flow pipe and twelve 

 11/4-inch returns, distributing the re- 

 turns under the benches. 



