90 



The Florists^ Review 



January 30, 1019. 



four feet of board wall on the north 

 side. In the house 20x100 use seven 

 1%-inch returns and place thirteen re- 

 turns in the north house. As the main 

 return from this part of the range, use 

 a 1%-inch pipe for the drip from the 

 north house and enlarge it to l^^-inch 

 before connecting the third house. 

 After reaching the boiler house, the two 

 returns may be united and connected 

 with the steam trap. 



The steam traps listed in our advertis- 

 ing columns are among the best that 

 are made. Select one that will handle 

 the water from 3,500 square feet of 

 radiation. 



The radiation that has been suggested 

 for 60 degrees is as follows: For each 

 of the 18-foot houses, one 2-inch flow 

 or two 1%-inch flows and five or six 

 1^-ineh returns; for 50 degrees use one 

 or two less returns. For the long 35- 

 foot house, two 2-inch flows and nine or 

 ten 1%,-inch returns; for 50 degrees use 

 two or three less returns. For the 37- 

 foot house, two 1%-inch flows (in addi- 

 tion to the 3-inch main) and eight or 

 nine 1^4 -inch returns; for 50 degrees 

 use two or three less returns. For the 

 20-foot house, seven 1*4 -inch returns; 

 for 50 degrees use one less return. For 

 the house 35x80, thirteen 1'4-inch re- 

 turns; for 50 degrees use two less re- 

 turns. 



All of the heating pipes, both flows 

 and returns, should be given a slight 

 fall, about one inch in twenty feet be- 

 ing sufficient for the flows and one inch 

 in fifteen feet for the returns. There 

 should be an automatic air valve near 

 the lower end of each coil. To shut off 

 and regulate the heat in the different 

 houses, there should not only be shut- 

 off valves near where the flows and re- 

 turns connect with each of the coils, but 

 one-half of the pipes in each coil should 

 have valves at both ends. 



SCKANTON, PA. 



B. E. & J. T. Cokely have purchased, 

 from the Baur Floral Co., Erie, Pa., 

 that part of the Baur business which 

 was connected with the manufacture 

 and sale of carnation menders, the 

 pliers and staples. The business will 

 be removed to Scranton and consoli- 

 dated with the Cokely interests. The 

 Messrs. Cokely state that the manufac- 

 turing end of the business was in such 

 shape that it was necessary for them 

 to have the machining reequipped, but 

 that they expect to push the department 

 much harder than it ever has been 

 pushed, even before the death of A. J. 

 Baur, who was the one of the Baur 

 brothers who handled this part of the 

 business at Erie. 





Stacks, tanks, roofs and all other 

 exposed metal or wood work shoald 

 be protected by 



DIXON'S SUici-Gra»h)te PAINT 



It srives years of service and suc- 

 cessfully withstands dampness and 

 other deteriorating agents. Write 

 for Booklet No. 64-B and long ser- 

 vice records. 

 Made in Jersey City, N. J,, by the 



Jateph DixM CrnciMe CaMpaiy 

 Established 1827. 



Mention The Reriew when you write. 



PIPE 



Wrought Iron of sound second-hand quality 

 with new threads and couplinK, 16-ft. lengths 

 and up. Also pipe cut to slcetcti. We guarantee 

 entire satisfaction or return money. 



ALSO NEW PIPE AND FITTINGS 



Pfaff & Keiidall,F£;^.i». Newark, N. J. 



Save Coal on Greenliouse Boilers 



May w« send you on a month's trial, prepaid, a Coggeshall 

 Air Tube Cleaner to clean your boiler tubes? It creates 

 its own air pressure with the use of low pressure steam. 



Specially Adapted for Greenhouse Boilers 



It cleans your boiler perfectly in four minutes, while running. 

 It does away with the hand method. It saves its cost before 

 the trial is ended. It can be returned, express collect, if you 

 do not find it to your interest to purchase the cleaner. It lasts 

 a lifetime. There are thousands in use. The price is $12.00. 



WRITE FOR ILLUSTRATED CIRCULAR 



TheCoggeshall Co., 121 Liberty St, NewYork 



Mention The Review when yon write. 



IMICO 



Hot Water Boilers 



Hade by 



Illinois Malleable Iron Co. 



1801-1825 DKcney Booleviri 



CHICAGO 



Avs noted for COAL ECONOMY and 

 good results generally. 



SKND FOR CATALOaUK 



Mentton The Bsrlew when yon write. 



PIPE CUT TO SKETCH 



TUBING, ALL SIZES 



SECOND HAND PIPE 



Large stock, all ■ins, famished with new threads and couplings. 



vAMES Fa GnlFrlTn) Philadelphia, pa. 



Mention The BeTlew when yon write. 







^ 



BOILER FLUES 



We nuke a tpedaltr of hsndUng 

 esrefnlly selected Boiler Fluea, i-ln. 

 diameter and other sixes, for Kreen- 

 hoose pipinc, Gutter Postik etc. Also, 

 we make a specialty of flues for 

 retnbins boilers. All flues are 

 thoronctily cleaned inside and oat, 

 trimmed, and are ready for use. 

 General Sales Aarent* for Stnttle's 

 Patent Clamp ana Klbow for joiiAtg 

 flues— no packinK, no leaks. New 

 standard pipe and all kinds of green- 

 house fittinrt. Riffat prices and 

 prompt shipment. 



H. MUNSON 



Est. 1898 Phone Superior S72 

 1488 Wells St.. Chicago 



% 



Mention The BeTlew when yon write. 



To stop that 



pipe leak per- 

 manently— 

 cheaply— use 

 Emergency 

 Pipe Clamps. 



M. B. SUner Cs. 



551-582 Wssirisitsa 

 lwl.^Ckiesis. 



BEST RED POTS 



BAR NONE 



Send for a sample and see for yourself— 

 or cive us a trial order at these net prices. 



PerlOOO 



2 -Inch S 600 



214-inch 6 80 



2ia-inch. 8.00 



3 -inch 10.40 



3>«-inch 12 80 



PerlOOO 



3%-inch $14.40 



4 -inch 1600 



4»fi-inch 2L60 



6 -inch 28 80 



6 -inch 43.20 



F. 0. B. Factory 



KAHLER POTTERY CO. 



921 OMAHA NAT'L BANK SLOG. OMAHA, N EB. 



Mention The Bevlew when you write. 



A HALMNCH ADVERTISEMENT 



here will Iceep your name and specialty 

 before ..the wliole. tiiade.^t a cost of 

 only 50c per week on a yearly order. 



■i^ri' .-I 



