SVFTEUBBB 11, 1919. 



The Florists^ Review 



101 



IT PAYS TO U 



PIA^Tir FIRP RffirV in all your boiler work. 



LLIiJllV/ liaL Ullltn Any handy man can install it 



Use it for patching when you cannot afford to cut a boiler out. 

 ELASTIC FIRE BRICK can be used for all fire brick purposes. 



Hoerber Bros., G«>o. Wittbold Co., Miller Bros., C. Haasermann, John Reading and Broadbeck the Florist 

 are using Elastic Lining. These are only a few of the thousands we are selling. 



IT COMES IN BARRELS READY FOR USE. A TRIAL ORDER WILL CONVINCE YOU. 



CURRAN & COMPANY 



Tel. CANAL 1013 1163-67 W, Twentieth Street, CHICAGO, ILL. Address Dept. 6 



Mention The ReTlew when you write. 



WILIS SELF.FEEDMG 

 HOT WATER BOILER 



fm &»iioiiiy, Durabilily,Dependability 



Instafl a WILKd 

 and forget your 

 troublM* 



No night lire* 



man required— 

 as the magazine 

 orooal chamber 

 holds sufficient 

 fuel to keep fire 

 10 to 12 hoars 

 without atten- 

 tion. Best made 

 for a small 

 greenhouse. 



tknd forCatoloeBB 

 and PrloM 



T. 



866 



S. WILKS 

 MFG. CO. 



•621 MMis In.. 

 CHICAGO, ILL. 



^Tentlon The Review when you write. 



will run north and south, the grade 

 sloping towards the north making the 

 average height of the side walls eight 

 feet. 



We wish you would recommend a suit- 

 able heating plant for this climate and 

 give the information necessary for in- 

 stallation. E. G. Co.— Okla. 



The temperature required in the 

 greenhouses is not stated, nor is the 

 piinimum outside temperature given. We 

 infer that a temperature of 60 degrees 

 will answer for the house growing flow- 

 ers and 50 degrees for the vegetable 

 house. In making the estimate we 

 considered that the outside temperature 

 seldom dropped below zero. Under these 

 conditions we would suggest a boiler 

 with a rating of 1,600 square feet of 

 hot water radiation be selected and we 

 would also provide radiation to the ex- 

 tent of 800 square feet in the warm 

 house and 600 square feet in the cool 

 house. If these conditions are not cor- 

 J'ect, the matter can be readily adjusted 

 oy using one or two return pipes more 

 0' less than suggested. 



i 



giiiiiiiniiniiniinniniiHHinuiiiiiniiiioiiHimiunnimiNiioiiiiimiucniiiMiinoiiiiiiiiiioinniiiiuramiHiimDimin 



BERNHARD 

 BOILERS f 



have made an enviable S 

 rppuiatioo among fl >r)Sis. S 

 The Bernhard is a worker S 

 and producer— not a lag- = 

 gard. = 

 Give your heating prob- s 

 lem serious cunsidera- = 

 tion. It means a great s 

 deal to know yuu havn a = 

 Boiler that can lie de- = 

 pendrd upon. 3 

 Catalogue "I" is fully S 



^^^^^^^^^^^^^^^^^^^^^^^^^^HMmMMH^B reauest. You 

 ^^^^^^^^^^^^^^^^^^^^^^^^^^^^^§^^^^y^^V know ab ut 

 ^^^^^^^^^^^^^^^^^^^^^^^^HHHHHHHB^^^ able greenhouse boiler. 



^'Lowest Water Line" | 



One of our 20 features. = 



I 101 Park Ave.. KANAWHA MFG. COMPANY Charleston. | 



I Kew York City 175 W. Jackson Blvd., Chicago, 111. W.Vs. | 



3uniuuiiiiiiiiiiiic]iiwiiniiaiiiiiiiinioniiiiiHiic]Hiiiiiiiiiic]iiiiiHiiiiic]iiiiiiiiiiiic}iiiiiiiiiiiic]iiiHiniiiiaiiuiiniiioiiHniimt]m 



Mentio n The Review when you write. 



IMICO 



Hot Water Boilers 



Made by 



Illinois Malleable Iron Co. 



1801-1825 Divcrsey Boidevinl 



CHICAGO 



Are noted for COAL ECONOMY an4 

 good results generally. 



SKNO FOR CATALOaUl 



Mpntion The ReTlew when you write. 



TUBING, ALL SIZES PIPE CUT TO SKETCM 



SECOND HAND PIPE 



Large iteck, all lixei. furnished with new threadi and etufliags. 



JAMES F GRIFFITH, ""^'I-S-JTa^'^ph,* pa. 



In each house we would use three 2%- 

 inch flow pipes, placing one on each 

 wall plate and the other two feet be- 

 low the ridge. There should be twelve 

 2-inch returns in the warm house and 

 nine returns in the cool heuse. They 

 should be arranged in three coils in 

 each house and connected with the over- 

 head flow pipes. 



Pipe and Tubes 



MX SIZES CIT TS SIHCI 



Philadelphia Second Hand Pipe Supply 

 1003 N. Tth St. PHILADELPHIA. PA. 



Mention The Rerlew when you writ*. 



