118 



The Florists' Review 



July 7. 1921 



SPECIMEN PLANS 



FOR A 



Modern Heating System 



are given in the new catalogue of all-steel 



WILKS HOT WATER BOILERS 



The self-feeding feature keeps an even 

 and continuous fire for 12 hours and long- 

 er without any attention. This makes 



NIGHT FIRING UNNECESSARY 



WRITE TODAY fOR YOUR COPY or OUK CATALOGUE. II'S rREE. 



S. WILKS MFG. CO. 3523 Shields Ave.. CHICAGO 



IT PAYS 



TO USE- 



ELASTIC FIRE BRICK 



In All Your 

 Boiler Work 



Any Handy Man Can Install It. 



Use it for patching when you cannot afford to cut a boiler out. 

 ELASTIC FIRE BRICK can be used for all fire brick purposes. 



Hocrber Bros., Geo. Wlttbold Co.» Miller Bros., C. Hausermann, John Reading and Broadbeck the Florist 

 arc using Elastic Lining. These are only a few of the thousands we are selling. 



IT COMES IN BARRELS READY FOR USE. A TRIAL ORDER WILL CONVINCE YOU. 



Tcl. CANAL 1013 



CURRAN & COMPANY 



1163-67 W. Twentieth Street, CHICAGO, ILL. 



Address Dept. 6 



handle the radiation to be built later. 

 If fully up to its rating, the Princeton 

 No. 10 will probably handle a second 

 house of the same size, by hard firing. 

 To heat the house shown in the sketch, 

 which is approximately 25x42 feet, with 

 two and one-half feet of glass in both 

 side walls, if both ends are exposed, 

 it would be well to use five 2 1/^ -inch 

 flow pipes, placing one on each side 

 wall plate, one on the purlin posts, and 

 the other three feet under the ridge. 

 Fifteen 2-inch returns will be needed. 

 Arrange them in'five coils of three pipes 

 €ach and connect each coil with one of 

 the flow pipes. Run both flow and re- 

 turn pipes downhill. 



DIFFERENT TEMPERATURES. 



We are going to erect a greenhouse, 

 which will be 21x100 feet. It will be 

 six feet high at the caves and eleven 

 feet one inch high at the ridge. It will 

 have three feet of glass in the sides, 

 two glass gables and 3-foot concrete 

 walls. There will be a division in the 

 center of the house. We shall have two 

 side benches, each four feet six inches 

 wide. The house will run east inid 

 west, and we intend placing the l)c)iler 

 in the east end. The division at the 

 east end is to have GO degrees of tem- 

 perature, while the west end must be 

 kejit at 50 to 55 degrees. How can we 

 arrange the piping and what sizes are 

 best to use? D. & C— Ont. 



The method of heating is not stated, 

 but we infer that hot water will be 

 Used. Bettor results mav be secured 



The Jaeger Mixer 



Get away from the everlasting repairing of 

 wooden benches and side walls of your Green- 

 houses—Build them of Concrete. 



Make your Service Buildinx and Boiler Room 

 fire-proof and substaniial. A Jaeder Mixer 

 will make it easy and economical to do. 



The price of the Mixer on Skids is only 

 $54.00 for belt power. This Mixer is a sturdy 

 machine, weighing 430 lbs. and built to last a 

 lifetime. 



Kor more particulars write to 



THE JAEGER MACHINE CO. 



526 Dublin Ave.. COLUMBUS. OHIO 



It Lets the riorist Sleep 



Let us tell ynn what one I YoU dOH't haVO tO Sit Up BHd WatcH 3 



;^:i!,-'K:^i^i;;r^^:L,;;M giblin greenhouse boiler 



WRITE NOW GIBLIN & CO. UTICA, N.Y. 



if the boiler can be lowered so thftt it 

 will ])e lower than the returns. 



For the railutting surface we would 

 run four overhead mains the length of 

 the house, using 2i;.)-inch pipes and 

 jilacing one on each wall plate and the 

 others either under the ridge or on the 

 ]>urlin ))osts. For the west end, to pro- 

 vide 50 to 55 degrees, eight 2-inch re- 

 turns will be re(iuired. To give 60 

 degrees at the east end of the house, 

 four additional return ]ii{)es will be 

 needed. To gui)ply them run a I'/i-inch 



TO AVOID TROUBLE-Use 



FISHER STEAM SPECIALTIES 



LOOK for our ad in July 14 issue 

 FISHER GOVERNOR CO. 



Home Omce -MARSHALLTOWN, lA. 



Blanche- in Principal Cities. 



Mention The Review when you write. 



fiipe from each overhead flow pipe, con- 

 necting them just east of the partition. 

 Arrange the return pipes in four coils. 



