156 



The Florists^ Review 



Mat 18, 1022 



WIZflRb 



TRADE 



BRAND 



MARK 



WITH A KICK IN ITII 



Shaep Manure with a kick in it 1 That's WIZARD BRAND because Wizard 

 Brand is best quality Feeding Station and Stock Yard Sheep Manure. Not 

 leached out, air-dried western corral manure with 15^ to 20<](i moisture. 



Wizard Brand is new, fresh stock, dried and sterilized by high-temperature direct-heat process that 

 always makes a bone-dry, uniformly pulverized product: weed seed, fungus and disease germs 

 destroyed, highly concentrated, always safe and dependable. The highest standard of quality in 

 Pulverized Sheep Manure. Unequaled under glass or in the field. 



Insist on WIZARD BRAND through your supply house or writ* us direct. 



THE PULVERIZED MANURE CO., 33 Union Stock Yards, CHICAGO 



is to be used, it will not be advisable 

 to attach more than 1,000 or 1,200 

 square feet of radiation. Even if the 

 houses have no glass in the walls, it 

 will require about 1,280 square feet of 

 radiation for 40 degrees when it is 10 

 degrees below zero outside. 



HEATING FOB BOSES. 



I expect to construct, within the next 

 few months, two rose houses and one car- 

 nation house, each of which will be 

 36x200 feet, running east and west. 

 There will be two glass gables in each 

 house. The side walls of these houses 

 will be eight feet high, with five feet of 

 glass. The two rose houses will open 

 together, but there will be a glass par- 

 tition between the rose and carnation 

 houses. 



It is my intention to use two 1%-inch 

 returns under each of the five benches 

 in the carnation house, on the north 

 side, and also two 1^-inch returns on 

 the north wall. The rose houses will 

 each have six benches, with two 1%- 

 inch returns under them. 



Do you think two 214-inch mains will 

 be suflScient, in each house, to take 

 care of this amount of radiation in re- 

 turns? I will place one 2%-inch main 

 on the purlin posts down the middle of 

 each half of each house, to distribute 

 the heat overhead from the mains more 

 evenly. 



The temperature required in the rose 

 houses is 60 degrees, when the outside 

 temperature is 15 degrees below zero, 

 and the temperature required in the 

 carnation house is 55 degrees. Low- 

 pressure steam is to be used. 



W. E. C— Minu. 



The radiation suggested for the car- 

 nation house and for the inside rose 

 house would be ample, and it could be 

 supplied by two 2%-inch flow pipes in 

 each house, but for the outside rose 

 house, with over five feet of glass in 

 the exposed wall, a slight increase in the 

 radiation will be desirable, and an addi- 

 tional 2M!-inch flow pipe should be put 

 in on the outside wall plate. Two ad- 

 ditional returns should be placed on the 

 south wall, and the returns under the 

 south bench connected with the third 

 flow pipe. 



The arrangement of piping is an ex- 

 cellent one, but it is preferable to use 

 1%-ineh pipes for the coils in houses less 

 than 250 feet in length. This merely 

 calls for two additional returns in each 

 house, which will make it possible to 

 place two returns under each gutter, and 

 will be helpful in melting the snow in 

 the gutters. For the same purpose, it 

 would be well to run the flow pipes on 

 the gutters instead of at the purlins, 

 especially as the heat is needed there 



"FAULTLESS" 



When a letter and check were recently received by us. addressed to the "Faultless Fire 

 Brick Co.." we were duly impressed by the clearsightedness of our customer. "Faul less" 

 exactly expressed our own opinion of 



FURNACE, LINING 



PLIBRICO is jolntleas. It allows no intake of air or escape of gases through the boiler 

 setting. It resists heat up to 3100" F. It minimizes shutdowns for repairs and replacements 

 of boiler settings. It everywhere proves itself a saver of fuel, time and money. 



Thousands of firms have been convinced through use that PLIBRICO is faultless. 

 Let us convince you. 



Send for our book, D-64, on "Modern Furnace Building," and ask to have our nearest 

 representative call. Our service is free. 



PLIBRICO U de- 

 livered only ia itecl 

 coBtainen of dii- 

 tiBctireappraruice 

 u tkewB >t tbe 

 rifht 



Warehouse 

 stocks In all 

 principal cit- 

 ies. 



UentloD Tbe R»Tlew wh«s roa writa. 



To stop that 



pipe leak per- 

 majiently — 

 cheaply — use 

 Emergency 

 Pipe Clamps. 



B. Skinner Co. 



558-562 WuUBftaa 

 B«al., CUcafO. 



PIPE and FLUES 



A LL SIZES of second-hand pipe, with 

 •^ new threads and couplings, in ran- 

 dom lengths or cut lengths. Also 

 make a specialty of handling boiler 

 flues for retubing boilers or for green- 

 house piping. All flues are trimmed 

 and thoroughly cleaned by machine. 



JOHN GROH 



1885 Ciyboani Ave, CHICAGO, ILL. 



Flues 



1 



Cleaned by Special Process 



Cut to order for retubing 

 Random lengths tor piping 



Guaranteed: Rebuilt Boilers 



STEAM and WATER ^v 



Prompt 1 Delivery t^ . ^B 



C. B. ISETT & SON 



BOILER WORKS. 

 1701-7 Winnebago Ave., CHICAGO 



TO AVOID TROUBLE- Use 



FISHER STEAM SPECIALTIES 



LOOK for our ad in June 8 issue 

 FISHER OOVERNOR CO. 



Home OfBce-NARSHALLTOWN, IA. 



Branches in Principal Cities. 



Mention The Rt^Tlew whc» too wrlf . 



PIPE — Second-Hand 



AU sizes Fittings and Boiler Tubes 



Pipe cut We guarantee entire satisfac- 



to sketch tion or money refunded 



Philadelphia Second-Hand Pipe Supply Ce. 



1003 N. 7th Street. PHIUDELPHIA. PA. 



■PIPE- 



Wrousht Iron of sound second-hand quality 

 with new threads and couplings, 16-ft. lengths 

 and up. Also pipe cut to sketch. We guarantee 

 entire satisfaction or return money. 



ALSO NEW PIPE AND FITTINGS 



Ff aff & Kendall, f^"^ Newark, N. J. 



