Jl'i.v 31, 1013. 



The Florists' Review 



79 



YOU COULD 



COMMAND 

 THife -SUN ! 



You would have the same control over the 

 temperature of your houses as is afforded 

 by an installation of the 



^ZDg^ t to Boiler I > 

 SYSTEM 



HE Morehead Return Steam Trap is especially designed and constructed 

 for Krtenhouse steam heating plants. It fills the dual capacity of 

 steam trap and feed water pump. It will create condillons enabl- 

 inK the florist to grow better flowers: save on fuel, water 

 and labor bills, and derive jreneral all around satisfaction 

 from the installation. 

 Write for particulars. 



Address Dept. "M " 



Morehead Manufacturing Co. 





DETROIT, MICHIGAN 



STOCKS CAKRIKD IN 

 Wichita. Kan. Philadelphia 



Trial. 



New York ChlciiKK Wichita. Kan. Philadelphia MemphlH. Tcnii. 



New Orleans, La. BliinlnKham, Ala. San Franclnoo / Los Angeles 



In Canada— Canatllan Morehead Mf»f. Co., Ltd., Woodstock. Ont. 



)^emphiH, ' 

 CO / Los Ai 



Mention The RhtIpw wIipii tiiii writt- 



GET WISE 



TO THE FACT 



You Will Save Coal 



by installing The Martin Rocking^ Grate. Costs a little more 

 than ordinary grates, but the coal bums— it doesn't go into the 

 ashpit. 



We refer to Peter Reinberg, Emil Buettner, Bassett & Washburn, Wietor Bros.. 

 Adam Zender, Sinner Bros., Albert Dickinson Seed Co., and many others. 

 They will tell you to order the Marttn Rooking Grate for the new boilers 

 to be put in this season. Write for catalogue and prices. 



343 So. Dearborn St 

 CHICAGO 



NARUN GRATE a, 



Send order no'vr— we 'will make up the gyrates and hold until you say ship. 



Only twenty-seven feet of the north 

 side is exposed to the weather, the rest 

 of that side being protected by another 

 greenhouse and a coal shed. Will this 

 be sufficient piping for carnations and 

 lettuce, in this Indiana climate? 



I also wish to heat an outside hotbed, 

 4x55 feet, at the south side of the 

 greenhouse. Would it be better to tap 

 the lower end of the coil, at the east 

 end, or to place a saddle just back of 

 the 3-inch valve at the boiler and run 

 a separate 1^-inch line across, with a 

 valve near the boiler, and connect with 

 the hotbed f Will five 1-inch returns in 

 the hotbed be sufficient? Can I tap 

 the lower 1^4 -inch return of the south 

 coil for a return from the beds, or 

 would it be better to run a pipe across 

 the building to the 2-inch return at the 



FOR A STKaPY PUKSSUWE 



THE HUGHSON REGOUTIRG 

 VALVE 



HUGHSON STEAM SPECIALTY CO. 



8021-3 S. Sf te St.. Chlcage 



boiler? I wish to grow lettuce in the 

 hotbed in the coming winter and sweet 

 potato plants in the spring. B. A. A. 



It is a mistake to use l'/4-inch and 

 1-inch pipe for returns in hot water 

 heating. In the house described it 

 would have been better to use five 1%- 

 inch pipes on each side, instead of 

 the seven 1%-inch and seven li4-iiich 

 pipes which have been used. If well 



BYERS' 



Gunnteed Full Weight Wrooght Iron Pipe 



Lap- Welded in sizes over IH-inch. 



nniNGS. VALVES, BOILERS, RADIATORS, ETC. 

 JOHN MANEELY, 



309^1-313 Arch St., PHII^DELPHIA. PA. 



Mention The Review when you write. 



READING GUARANTEED 



Wrought Iron Pipe 

 Nelson Valves 



All Sizes In Steck. 



The Harttnan Company 



1231-5 No. Front St., Philadelphia 



Mention Tbe Rerlew when yoD write. 



