86 



The Florists' Review 



ACOCST 



191£ 



GreenKbuse Heating 



is a perplexing question to all florists 

 except those using -^ 



Morehead Steam Traps 



HAVE you ever talked wltb a brother florlat who uses Morebead Return 

 Steam Traps? If not, do so at first opportunity and be convinced that 

 you must Install one at once. 



There are more MORBHKAD TRAPS installed in greenhouses than of all other 

 makes of steam traps combined. The Morehead is distinctly a florist's trap. Every 

 feature of its construction has been treated with a-*iew of meeting the*speclal npeds 

 of the florist. 



. Send for a trial Trap. 



MOREHEAD MANUFACTURING COMPANY 



DEPT. "M," DETROIT, MICHIGAN 



Wichita. Kw. 

 New Oble.'iiis, La. 



-STOCKS CARRIKD IN- 

 Philadblphia 



BlBBONOHAM, ALA. 



Memphis, Tenn. 



Los AMOSLE8 



WooDiJTocK, Ontario 

 San Fbanoihco 



the needed temperature with two less 

 returns. 



For heating the proposed extension to 

 the present house, it is suggested that 

 the 3-inch main be reduced to 2i/->-inch 

 and extended to the farther end of the 

 extension. Disconnect four of the 2- 

 inch returns from the present main and 

 extend them to the farther end of the 

 house, and connect with the end of the 

 2^-inch main. The other return pipes 

 need not be changed, and will still be 

 connected with the end of the 3-inch 

 flow pipe. This will give one 3-inch 

 flow and six 2-ineh returns in the pres- 

 ent house and one 2V^-inch flow and 

 four 2-inch returns in the extension, and 

 the latter will maintain \ temperature 

 about 10 degrees lower than is now 

 secured. As no plan of the houses was 

 submitted, no definite advice can be 

 given about the exact location of the 

 returns, but good results can be secured 

 if they are ui)on the walls as suggested. 



SESIDENCE AND OBEENHOUSE. 



Will you kindly submit the enclosed 

 sketch to your heating expert? Can I 

 heat the residence and conservatory if 

 the piping is arranged as indicated in 

 the sketch, or must 1 have a separate 

 return pipe for each radiator? The 

 boiler is in the cellar, which is ^ven 

 feet deep, and the expansion tank is in 

 the garret of the residence. W. F. H. 



The sketch shows a number of radia- 

 tors through which the flow pipes pass, 

 and return pipes running from the far- 

 ther radiator in each series to the boiler. 

 While this plan of arrangement might 

 be used when no more than two radia- 

 tors are to be connected, it will be bet- 

 ter to run a flow pipe under each series 

 of radiators and then connect each of 

 the radiators directly to this pipe. A 

 return pipe should be run in the same 

 manner and connection made with each 

 radiator. 



NEW ORLEANS, LA. 



The Market. 



The last two weeks of July were the 

 busiest ones the retailers have had for 

 9, long tiflie. The sudden death of Mor- 

 gan Whitaey, July 18, called for the 

 most artistic and expensive ftwrerai 

 work of «U descriptions that some of 

 the local HoHsts ever had to make up, 



Superior in Name- 



"The Superior boiler 

 has them all beat for 

 greenhouse heating" 



is what the grow- 

 ers all say who 

 are using them. 



Superior in Fact 



The SUPERIOR STANDARD is designed specially for green- 

 house work after a close study' of what was needed. It is easily 

 cleaned, although it has more flues than any other boiler, but — more 

 flues give more heat; more flues require less fuel; the water heats 

 quicker' and hotter, because the volume of water heated by each 

 flue is smaller. 



All we ask is a chance to show you. 



Write Today for Catalogue 



Superior Machine & Boiler Works 



Superior and Green Sts., CHICAGO, ILL. 



=Save V3- 



of your fuel bill by heating 

 your 



GREENHOUSE 



with soft co»I in a 



SMOKELESS 



Kins I^Ml BoU«r. 



Write ai ior information. 



KWG CONSTKUCnON CO. 



27 Kit's iMi NM4liTntwuli,llY. 



ALL THS SUNLIGHT ALL DAY HOUSES. 



BOILER FLUES 



(I 



We make a apedalty of handUng caretally selec^ 

 Boiler Fluea. 4-inch diameter and other slz«>^ i°l 

 greenboiue piplne, Ootter Poati, etc. Alao, **' 

 make a apecVklty of floea for retobinc boiler*. ^' 

 floe* are thoroofffalr cleaned and trimmed, rea<V 

 for oae. General Sale* Agents for StatUe's r»<»^ 

 Olamp and sabow for Jatntag flnee— ao packlne. °" 

 leaks. New standard pipe and all kinds of greeo- 

 honse 0tting8. Right prices and prompt shipmeD'- 



H. 



1405 Wells St. 



MUNSON 



Phone Korth Bt: Chic«»<' 



