500 



The Weekly Florists' Review* 



August 4, 1004. 



PIPING. 



We have a greenhouse running east 

 and west 16x75 feet, north wall five feet 

 six inches, boarded up, south wall thirty 

 inches of glass and thirty-six inches of 

 boards. The west end is boarded up 

 and the east is board and glass, the same 

 as the south wpU. Even span, eleven feet 

 from ground to gable. We have a No. 

 186 Ideal water back heater that we wish 

 to use. With a 3-inch supply pipe run- 

 ning the full length seven feet from the 

 ground and 1^/^-inch returns, how many 

 runs under benches will it take to keep 

 a temperature of 60 degrees in z%^ 

 weather? The boiler is supposed to hav^ 

 a heating capacity of 1,025 feet. Will 

 the boiler maintain this temperature? 

 Would it be better to have the supply 

 pipe under the middle bench? F. G. 



If, as you state, your boiler has a 

 capacity for 1,025 feet of radiation it is 

 amply large to heat nearly double the 

 space you now have, as your house will 

 require only about 540 feet of radiation 

 to maintain the desired temperature with 

 water at 180 degrees. You will undoubt- 

 edly get good satisfaction from carrying 

 the main flow pipe near the ridge to the 

 far end of the house and there dividing 

 it to supply coils under the side and mid- 

 dle benches, or, if it is more convenient 

 to carry the supply pipe under the cen- 

 ter bench, the number of returns under 

 the bench can be reduced and the heat 

 evenly distributed by increasing the num- 

 ber of returns under the side benches. 

 In either event you should use, in addi- 

 tion to the 3-inch flow pipe, twelve 1^- 

 inch returns. These may be distji-ibuted 

 under the benches in the house so as to 

 provide an extra pipe along the side most 

 exposed. L. C. C. 



Shibemanstovpn, Pa. — John F. Rupp 

 reports orders coming in at a most grati- 

 fying rate and all hands rushed in get- 

 ting them out promptly. 



Amsterdam, N. Y. — Mrs. Frank Ho- 

 taling, wife of the florist, lies dying from 

 grief, caused by the absence from home 

 of her ■20-year-old son, William. Young 

 Hotaling left his home, July 24, in the 

 early hours of the morning, without any 

 apparent cause. 



Ventilating 

 Apparatus 



The Wolf Improved System is 

 the moat convenient and durable. 



One single machine operates houses 50 

 to 400 feet long. One No. 6 double ma- 

 chine operates houses 200 to 700 feet long. 

 We also furnish the latest improved pipe 

 machines and the Wolf Dump Sieve Soil 

 Sifter. Send for references and catalog. 



A. Q. WOLF & BRO., Dayton.O. 



Mention The RptIpw when yon write. 



Holds Class 

 Firmly 



See the Point MT 



TlM Taa Server P«^ 

 l%«t filaalM PSm* »M 

 th» bMt. HO rishU wr 

 l«fla. Box of iwe point* 

 n o«Bta> poatpaid. 

 HEWBT ▲. DREEK, 

 TU ChMtaat B>.. PMIa., Ttu 



TI]£ BENCH OF THE FUTURE 



Practical, 

 ever- 

 lasting, 

 cannot 

 rot out. 



PatentB 

 pecdtng. 



80 per 



square 



foot 



complete. 



Send for 

 estimates. 



NIAGARA CEMENT & CONCRETE CO., Room 2, P. O. Bldg., North Tonawanda, N. T. 



Mention The Berlew when yon write. 



Are You Going to Build ? ^Z'ZZt^l^'^Z 



Our Catalogfue will give you many- hints, and may save you money. 



DILLON GREENHOISE MFG. COMPANY, 



BLOOMSBURG, PA. 



Mention Tie Review when yon write. 



Qarland's Gutters 



Will keep SHOW asd ICE 



Orr TOUB GLASS and PBSVBVT 



BBBAZAOS. 



OBO. M. OASLAHB, DBS PLAZXTBS. ILL. 



Mention The Review when you write. 



GREENHOISE VALVES 



Fittings 



and 



Ventilating 

 Apparatus 



Mention The U«t1cw when yoa write. 



Send for 



Catalog'ue. 



COLDWELL-WiLGOX COMPANY, 



ITBWBTrBOK. V. T. 



Mention The Review when yoti write. 



Wired Toothpicks 



Manafactnred hj 

 W. J. COWEE, BERLIN, N. Y. 



tO,OOO....S1.50; SO.COO... Se.as. sample tree 

 For sale by dealers. 



Mention The Review when you write. 



THE REGAN 

 ...PRINTING HOUSE... 



Catalogues 



87-91 Plymouth Place, Chicago. 



Atentlnn The Bievlew when yon write. 

 Always Kentlon the.... 



Florists* Review 



When Writinir AdvertiserB. 



KRAMER'S POT HANGERS. 



srnrsery.. 



..Seed... 



Florists'. 



Neatest, simplest, most 

 convenient and only practi- 

 cal device . for converting 

 ordinary flower pots Into 

 hanrintr baskets. They fit 

 all standard made pots from 

 2 to 10 inches in diameter. 

 The illustration shows how 

 they are attached. Just the 

 thlngr for hancrinir np Ferns, 

 Begonias, etc. You can make 

 room and money by their 

 use Try them. 



Price with wire chain, 

 as shown in cut, 91.00 per 

 dozen by express. SampK 

 dozen by mall, Sl.SS. 



I. N, Kramer & Son 



CEDAR RAPIDS, lA. 



For sale by the E. F. WINTBBSON CO., 

 CHICAGO ; C. C. POIiL. WORTH CO.. 



BaLWAUKEE, WIS.: TACOHAN'S SKED 

 STORE, NEW YORK and CHICAGO. 



Mention The Review when yon write. 



CIT FLOWER BOXES. 



WATERPROOF. Comer Look Style. 



The best, strongest and neatest folding 

 Sut flower box ever made. Cheap, durable. 

 To try them once is to use them always. 



SizeNo.t....Sz4 z20..t3.00perl00: tl9.00 per lOM 



3.00 •• 19JM) 



2.60 •» 



No. I.... 3x4^x16. 

 No. >... .8x6x18.. 

 No. S ...«x8xl8.. 



No «.... 3x5x34.... 2.76 



No. 6 

 No.e 



No. 7 



No. 8 

 No. 9.. 



.4x8x22. 



.4x8x38.. 



.6x16x20. 



.8x7x31.. 



.5x10x36. 



•• No. 10.. .7x20x20.. 



8.00 

 8.76 

 6.S0 

 8.00 

 6.60 

 7.60 



No. 11...3>iix6x30.. 8.00 ** 



•38.00 

 dOiOO 

 3860 

 86.00 

 64.00 

 88.60 

 62.00 

 67.00 

 28.60 



Sample free on application. Ko charge for print- 

 ing on orders above 360 boxes. Terms cash. 



The Livingston Seed Co., Colunibus,0 



Box 104. 



Mention The Review when you write. 



HITGNirSGS Sc GO. 



233 MERCER STREET. NEW YORK. 



VENTILATING APPARATUS 



IIOI VNMfR BOINKS, PIPfS AM) riITI\(,S. 



SEND FOUR CENTS FOR CA-^ALOGUE. 



j$jtj» X^ Alwayi mention the FIoTlSts' ReVICW wEen writing advcftiien. Jl Jl Jt 



