*B>^?/ j^-:'jrfT^T^_"'' ,~f^'~ '^\i-.-'ji^~!v!i^'\^7^i>^^^ -V ' j^i.^^fs, ^"•'p. 



1208 



The Weekly Florists^ Review* 



NOVBMBEB 3, 1904. 



► I.-"- 



CXDNDENSATION. 



In our plant we have eighty feet of 

 5-inch pipe, 600 feet of 2y2-inch, 6,000 

 feet of 1-inch and 4,600 feet of I14- 

 inch pipe, also 200 feet of 2% -inch 

 drips and eighty feet of 3-inch drips. 

 We carry a night temperature of 50 

 degrees, and want to know what the 

 maximum condensation per hour would 

 be in weather 20 degrees below zero, 

 and with all pipes working to full ca- 

 pacity. We are given widely varying 

 estimates as to the size of pump re- 

 quired. H. H. N. 



From the statement of pipe given 

 above the total number of square feet 

 of radiation in this plant is 4,973.96 

 square feet. This gives 1,492,188 Brit- 

 ish thermal units transmitted from ra- 

 diating surface per hour, which is equi- 

 valent to 1,544 pounds of steam or 186 

 gallons of water per hour. For sake of 

 safety and ample provisions, we will say 

 300 gallons per hour. I know of 

 no more accurate method of estimating 

 this than that here given. If you have 

 a pump with 300 gallons capacity per 

 hour it should be amply large to han- 

 dle the condensation. If, however, the 

 pump can only lift 300 gallons under 

 atmospheric pressure it will be at a 

 disadvantage when working against a 

 head of steam on the boiler, but if it 

 is a boiler feed pump there should be 

 no difBculty. L. C. C. 



INDIANAPOLIS. 



Trial of the suit for $1,000 damages, 

 brought by F. A. Conway & Co., florists, 

 Napoleon and Beecher streets, against 

 Anton Schmidt and Henry Cook, owners 

 of a brick kiln on Beecher street, has be- 

 gun. It iff alleged that soot and cinders 

 from smoke made by the brick kiln have 

 greatly injured the company's stock. It 

 is charged that the brick manufacturers 

 have violated the city smoke ordinance. 



We aeb much pleased with the Flor- 

 ists' Manual, and could not get along 

 without the Florists' Review. Enclosed 

 find another dollar. — Wm. Rhodes & 

 Son, Leechburg, Pa. 



ASTIM 



USejTNOW. 



F.O. PIERCE GO. 



170 Fulton St.. 



NCW VOHK 



Wired Toothpicks 



Mannfaotnred by 

 W. J. COWEB. BERLIN, N. Y. 



U,000... 91.50 ( 60,000... S6.25. Sample free 

 For sale by dealers. 



•eeoeeeaeeaeeea**! 



Holds Class 

 . Firmly 



I ' See the Point 



OIscIhk Folate are tbebeM. 

 No rights or left*. Box of 

 1.000 poinU T&eU. poMpkld. 



HENRT A. DREEK, 



T14 GkMtMt Bk, mia., fm. 



ny ^eeei>i>»w<ww^ew w * 



Montlon The Review when you write. 



Composition Posts, ilT^XJ"-^ 

 Composition Gutters, ss^p^W 



Freight paid where it does not exceed 80c per 100 lbs. 

 TKET ABE XVSESTBUCTIBIiB. '' 



TKST W1I.1. VOT BOT OB BUST. 



70V CAH DBIVE VAII.B XV THEM. 



These Posts and Gutters combine all the good qualities of Iron and wood. 



Dillon Greenhouse Mfg. Co., Bloomsburg, Pa. 



Montloti Thp Review when yon write. 



SEE THAT LEDGE. 



Pat. Sept. 18, 1900. V 



THE 



IMPRi 



JENNINGS 

 IRON GUTT ER. 



....USE OUR.... 



Patent Iron Bench Fittings and Roof Sopports. 



Ventilating Apparatus, 

 Improved Vaporizing Pans for Tobacco Extracts, Etc. 



•END FOR nil I CD PACVCV 9 on Snooesson to JEVEIVOS BBOS. 

 CIRCULARS. UlLLCIIy uAOIVCl OC WU«f S. «. Cm. UkiM lirtit Stt., PNIIADELPMIA, H 



Garland's gutters 



Will keep SHOW and ZOE 



Orr TOVB OLA88 and FBBVBVS 



BBBAZAOE. 



OBO. M. OABKAVD, DBS PZiAZVBB. ZXJb. 



Mention The Review when you wrlte^ 



w 



HEN YOU WANT 



Engravings made 



Bend US Photos or cllpplnsrs from other 

 catalogues and let us reproduce them. We 

 make the cuis for the Florists' Review. 



DEARBORN ENGRAVING CO.. 



300-306 Dearboni St. OKZOAOO. 



Mention The Rerlew when you write. 



GOT A BOONI! 



Morristown, N. J. 

 I must say the Fumigatinif Powder is the 

 best tbini; that ever happened; its eflect- 

 ivenets. simplicity in u&ing and all else 

 connected with it makes it a boon to us. 

 See page 11!)8. 



JAS. FRASER. 



Mention The Review when yon write. 



IIITGMI^OS Sc GO. 



233 MERCER STREET, NEW YORK. 

 tikbl^NMOl M, m ILDIXi. 



V ENTI L.ATI NO A F'PA RATU S 



MOI VWUR BOil!RS. Pli'l S \M) IIIIISJ-S. 



SEND FOUR CENTS FOR CATALOGUE. 



Mention The Review when yon write. 



