796 



The Weekly Floristi^^ Review. 



1<'KBRIARV 23, 1005.,, 



That Use It Say^«'THERE IS ONLY ONE," 



Mauabonkck, N. T. 

 I tried the 5 lb. trial package of The Famig'ating' Kind Tobaooo 

 Powder in two of my houees one night and the following nigbt I gave 

 a 60-foot bouse a tborougb smoking. Result : I would like you to send 

 me 100 lbs. of tbe Fumigating Kind. W. H. Danikls. 



Maywood, III. 

 Th* 7iimiGratlng' Kind Tobaooo Powdor is great stulT ; 

 it keeps one's bouses clean as a sheet. 



I can heartily recommend it./ - .. Albebl F. Amling. 



^ -V. ' 



HFREE trial five-pound bag: will cost you nothing: more than the express chargfes on it* The trial 

 bacf will prove our assertion that it is the most effective^ cleanest and quickest as well as the 

 cheapest (10 cents per 1 00-foot house) article to fumigfate with* Ail aphis ^Ued in one ni8:ht — 

 our booklet tells of it; we mail one on request. 



THE H. A. STOOTHOFF COMPANY, Tobacco Powder Hobbyiats, 116, 117, 118 West St., New York 



Mention The Review when 70a write. 



EXPANSION TANK. 



I expect to build two houses 18x80 

 to be heated by water in 4-inch cast- 

 iron pipes. Can I dispense with the 

 expansion tanks at the far ends of the 

 houses and have one large tank over 

 the boiler on the main flow? Are eight 

 runs of 4-inch pipes enough for a house 

 for roses and six pipes enough for car- 

 nations under weather conditions in 

 Kentucky? I have a No. 15 Hitchings 

 boiler. J* J- C. 



Yes, you can dispense with the open 

 expansion tank at the far end of the 

 house. Instead of a large tank con- 

 nected with the main flow it would be 

 l)etter to connect the expansion tank 

 with the main return near the boiler. 

 A 1-inch pipe tapped into the main re- 

 turn near the boiler and carried eight 

 or ten feet above into a 50-gallon tank 

 should provide ample expansion for the 

 system. Eight runs of 4-inch cast-iron 

 pipe should be ample for the rose house 

 if the boiler has capacity to maintain 

 water at 180 degrees. Six runs under 

 the same conditions should be ample for 

 the carnation house. L. C. C. 



TOO FEW PIPES. 



We have a new and well built house 

 25x60 feet and thirteen feet to ridge 

 heating with a Gorton No. 212 »4 boiler 

 set in a pit and burning egg coal. On 

 each side of the house there are five 

 rows of 2-inch pipe, also the center aisle 

 has two rows under benches, two rows 

 each side of the walk. In the recent 

 cold weather in New York we could only 

 keep 45 degrees at night. What is 

 wrong? M. O'C. 



If the house you mention, 25x60 feet, 

 contains fourteen runs of 2-inch pipe, 

 or in all 840 feet, it lacks 120 feet, or 

 two runs, of having sufficient piping to 

 maintain a temperature of 60 degrees 

 during cold weather with hot water at 

 180 degrees. It is not quite clear 

 whether the house contains fourteen or 

 sixteen runs of pipe. The boiler should 

 have a capacity sufficient to supply 

 about 800 feet of radiation, although 

 the sixteen runs of 2-inch pipe will only 

 provide- about 600 feet of radiation. 



L. C. C. 



PILVERIZED 



SheeplVlanure 



DBZED AXTD OBOUZTD. 



Mixes immediately with the soil. 

 For prices apply to 



NATURAL GUANO COMPANY 



AURORA, ILL. 



ICentlon The Review when you write. 



Pumpinf Engines 



. FOB ■ 



Florists and Gardeners 



Thty uu lit tr iimIIh for fnl. 



THE STANDARD PUMP AND 



ENGINE CO., 



OI.KyEI.AMD. - OHIO. 



Mention Tte Review when yon write. 



Wired Toothpicks 



Mannf sotnred by 

 W. J. COWEE, BERLIN, N. Y. 



njBn....mi.BOi tOJOOO... Se.SS. sample frM 



For ■»!• bT de«ler«. 



Mention Tb« Review when 700 write. 



For Sale, Greenhouse Material 



milled strictly of Louisiana Cypress. And will 

 cut and splice to order. Hotbed sash a spec- 

 ialty. Try V. E. Reich's Oxford Putty specially 

 made for greenhouse purposes. Estimate freely 

 lumisbed for Kreenhouse and hotbed glass. 



V.E. REICH, i^^S^^'AT Brooklyn, N.Y. 



Mention The ReTiew when yon write 



CEMENT 



BENCHES 



NIAGARA CEMENT & CONCRETE CO. 



North Tonawanda, N.Y. 



Always mention the Floriits' Review wlien 

 writing advertisers. 



We want room and for every order you send 

 the Cash with before March 1, 1905, you may de- 

 duct 10 per cent on the followtoff Ferns. Satis- 

 faction Guaranteed. 



Boston Ferns 



We quote Fine No. 1 Stock. We want to 

 call your attention to our prices on Ferna. Fin- 

 est stock. We would like a trial order and will 

 fuarantee to please you. Boston, per 100— 2^-in., 

 4: 3-ln.. 18; 4-ln., 116; 6-ln.. 126; 6-ln., 140. Each— 

 8-ln.. il to 11.50; 10-ln., 11.50 to $2.50. Plersonl. 

 per 100-2Ji-ln., t6; 3-ln.. 112.50; 4-ln., $20; 4-ln.. 

 $35. Eacb-6-in., 75c to$l: specimen plants, $150. 

 $2.50, $3.50 and $5. FINE ASPARAGUS— 

 Plamosas. per 100— 2-ln., $3.50 to $5; 3-ln., $6 to 

 $8; 4-ln.. $15; 61n..$25. Sprengrerl, per lCO-2-ln., 

 $260 tots 50; 3-ln., $3.30 to $5; 4-Tn., $10; 5-in., ri5. 



In sending for samples of any stock you want 

 to buy, send 50c or $1 00; then you get enough to 

 show you the quality of stock. 



GEO. A. KUHL, PEKIN, ILL. 



Mention The Reriew when you write. 



nw FsioB :li8t ov 



fv»M KAISER KRONEN stumrf 

 Bay Trees 



Orders booked now. 



JUUUS ROENRSCO.S^^^!%^*;: 



lientlen Tbe ReTlew when yea write. 



...PANSIES... 



London Prize Show Flowers, exquisite colors, 

 large transplanted plants from cool houses, 50c 

 per 100 by mail : $3.00 per lOOO by express. 



Oboonlca— 3-incb per 100, $8.00 



4-inch " 5.00 



Aspararas ■prang'en-4-incb. 5.0O 



PlTunoBUS— 4inch. 6.00 



C. WHITTON, . UTICA, N. Y. 



Itentlop The Berlew when jon write. 



RUDBECKIA PerlOO 



Extra choice, large clumps S6.00 



ASVAMAOVB BPUVOnX, Extra 



quality. 2>4-ln. poU 2.00 



ABPAKAQUW PXinXOSirS, Extra 



quality. 2^-ln. note 2.60 



ASPABAOV8 PLUMOSU8, Extra 



quality, 3-in. pots 4.00 



Above prices cash with order. 



JOHN BROD, Niles Center, lUinoia 



Mention The Review when yon write. 



Automatic Greenhouse VENTILATORS 



From $25.00 up. Send for circular. 

 The Safety Antomatlo Ventilator and 

 Heat Begnlator Co , £ake Oeorg'e, V. T. 

 Mention The Review when you write. 



PEERLESS SILPHIR BLOWER. 



"A great Improvement over the bellowe." 

 Price, 94.00 F. O. B. Ohioaro. 



MCMunnAN & COif cHicAoo, zu. 



Mention ne Review wten 70a write. 



