1086 



The Weekly Florists^ Review* 



September 28, 1005. 



The Whilldin Pottery Co. 



STANDARD FLOWER POTS 



Oar output ot Flower Pots is larger tban any concern in tbe World 

 Our Stock is always Large and Complete 



Main Office and Factory. 



713 WHARTON STREET, PHILADELPHIA 



Warehouses: JERSEY CITY. N. J. LONG ISLAND CITY. N. Y- 



Mention Tbe Review when rou write. 



F \L \0\R;nIXS,' t ■ , XWXAXa 



:.<pXxFXX|^^Xi^;RXxX;<'<H>ti>sD. 



ssv 



<X 



^4^x>^h<p^Kyiiyir^ixy^>m^<j<$^m^^ 



PIPING. 



We haTe three connected houses 12V^x 

 76 feet, east and west ; ridges eight feet, 

 side walls and gutters six feet, glass in 

 east end above three feet; south side 

 covered by a lean-to with five feet of 

 glass. We also have a detached house 

 8x37, nine feet to ridge and six feet to 

 plates. We -wish to heat,..Tvith hot water, 

 using 1^-inch and 2-inch pipe. The 

 temperature required in the three houses 

 is 55 degrees and in the lean-to 60 de- 

 grees when it is 15 degrees below zero 

 outside. How much piping is required! 



How many feet of 1%-inch pipe would 

 be required to construct a coil boiler to 

 heat these houses? B. & S. 



The three houses 12^x76 feet, to- 

 gether with the south lean-to compart- 

 ment, can be heated by using four 2-inch 

 risers to supply four coils of 1%-inch 

 pipe, each containing nine pipes; i. e., 

 thirty-six l^/^-inch pipes in the entire 

 range. It would be well to run one of 

 the 2-inch risers along the north wall, 

 in the angle formed by the side wall and 

 -sash bars, and to arrange one coil of nine 

 1%-inch pipes on this wall. Each of the 

 other three coils and supply pipes can 

 be arranged on the posts carrying the 

 gutters, arranging each supply pipe the 

 same height and on tbe same grade as 

 «very other in the system. The house 

 8x37 will require a 2-inch supply and 

 nine 1^-inch pipes arranged in two 

 coils, five on the most exposed side and 

 four on the most protected side of the 

 house. 



A boiler to provide for the piping in 

 these houses should have a capacity to 

 provide for 1,800 feet of radiation. If 

 constructed of 1%-inch pipe 450 feet 

 would be required. L. C. C. 



Belfast, Me. — Willis E. Hamilton 

 this year rebuilt a carnation house 20x 

 100 and plana to put up two more houses 

 150 feet long next season. 



BBB 8TAVBABD POTS. 



Price per 1000, f. o.b. Harrison: Trin-.tSM: 

 2}i-ln.. «2.70: 2>i-ln.. $8.26: 3-ln.. $4.26; 3H-in.. 

 96.60; 4-iD.. $6.80; Mn.. $11.00; 6-ln.. $18.00. OMta 

 must aecompaDT order. 

 KJLBBX80V POTTBBT. Harrison, Ohio. 



PEERLESS SULPHUR BLOWER 



"A jreat Improvement over the bellows." 

 Price, •4.00 F. O. B. Chicago. 



McMORRAN & uOi ckzoaoo, xu. 



•lleatloii The Berlew wtaes 70a write. 



KELLER POTTEIlY CO. 



Manufacturers of Florists' Red Ttpwer Pots, 

 Azalea Pots, Bulb and Fern Pant, Etc. 



Ttie very best sbippinir facjlltips on both PeBnaylraBfti R. B. and Philadelpbia j^Readlnr R. B. 



213 TO 223 PEARL STREET, NORRISTOWN, PA. 



BOILER REPAIRS 



JOHNSTON HEATING CO. 



Write to lu if your boilers need repairins 



or replaclDR. 

 OUBS ASS VOX TBUBT PSIOSS 



1 135 Broadway, NEW YORK 



Mention The Review when you write. 



FOR SALE.... 



New and Second-hand 



on&r OTPSBBS 



aBBBVKOUBB X^XTVBZB, 



HOTBBD 8A8K, 



OBBBBBOU8B OX.ABB, 

 BOX^BBB, 



PZPB AWD rZTTXHOB, 



BTBAM riTTIVa TOOXiB. 



HOBB AMD BOSS VAIYES. 



VBVTIXiATIVO APPABATUB 



Write for our prices on anything yoa may need 

 for tbe erection of your gre enbouses. 



METROPOLITAN MATERIAL CO. 



OrvenhoTia* Wreckers 

 1 398-1 408 Metropolitan Ave., Brooklyn, N.Y. 



Mention The Review when yon write. 



"Islklni gnat vii mr ichltnd 

 vilhHl •ithuilatn." 



We are enthiuiastic about our '\ 

 Syraoose Red Pots 



because we know that they 

 are made of best material 

 by tkilled workmen. 

 A trial order will convince. 



BTBAGUBK POTTEBT 00. 

 STBACVSK, N. T. 



Mention The Review when you write. 



Destruction 



To all Insect pests on your plants. 

 Try "NIcotiolde." 



THB MAXWELL MPQ. CO. 

 nth 5traet, LOUI8VILLB, KY. 



Mention Tbe Review when yon writ*. 



TheGem Support 



Open. PstcBtei. Olosei. 

 HAS ALL THE 



GOOD POINTS 



It is made of Galvanized Wire, two rings and 

 one stake wbicb are never taken apart. Can be 

 raised, lowered, made large or small according 

 to tbe size of your plants. Can be folded flat 

 and does not catch or tangle. Neat and so bandy 

 that you cannot afford to be witbout it. Write 

 now for prices. 



J. H. BROXEY, Florist, Dayton, Ohio 



Mention The Review when yon write. 



THE WOLF 



Improved VENTILATING APPARATUS 



Either Pipe Shafting or Cable machines, most 

 powerfal on tbe market. Equipped with Steel 

 Ratchet Arms and all Roller Bearing Hangers, 

 Send for descriptive catalogue, 



A. Q. WOLF & BRO. 



DAYTON, OHIO 



Mention Tbe Review when yoa write. 



