I20i 



The Weekly Florists^ Review* 



OCTOBEB 12, 1905. 



The Whilldiii Pottery Co. 



STANDARD FLOWER POTS 



Our output ot Flower Pots is lars:er,,tban any concern la tbe World 

 Our Stock is always Larg:e and Complete 



Main Office and Factory. •• * * 



713 WHARTON STREET, PHILADELPHIA ^ 



Warehouses: JERSEY CITY. N. J. LONG ISLAND CITY. N. Y. 



Mpntlon The Rfrlew when you wrltf. 



PIPE TO DWELLING. 



I would like to know if I can run a 

 2-inch pipe from my greenhouse boiler 

 125 feet to my dwelling, there to heat 

 three radiators? The dwelling is five feet 

 above the water line in the boiler but to 

 avoid the driveway the main would have 

 to drop to within six inches of the water 

 line in the boiler. Would this work, us- 

 ing the main to bring back the condensa- 

 tion to where a bleader could be taken 

 off to return it to the boiler t H. M. 



If, as you state, it is necessary to drop 

 the main flow from the boiler to the 

 house to within six inches of the water 

 line of the boiler, I think it would be 

 much safer to carry an independent re- 

 turn from the radiators to the boiler 

 rather than attempt to carry return 

 water back to the bleader through the 

 riser. It would be well to make the 

 bleader about i^.-ineh and run a por- 

 tion of it horizontally so as to allow the 

 use of a swing check to prevent the 

 water backing out of the main return 

 into the riser. Keep the main up as high 

 as possible, give it an even grade from 

 the off-set to the house and put the 

 bleader in the basement of the house and 

 make a swing joint connection between 

 the flow and return. L. C. C. 



AN ENCLOSED VERANDA. 



This fall I intend to enclose the east 

 and south sides of a veranda to be used 

 as a conservatory. It will contain 700 

 square feet of glass and about 6,000 

 cubic feet of air-space. It is to be parti- 

 tioned in two sections. What size of 

 boiler and what size and number of pipes 

 would you recommend to maintain a night 

 temperature of 45 and 60 degrees in the 

 respective sections? The temperature sel- 

 dom falls below zero here. Would it 

 be safe to use hydrocyanic acid gas for 

 fumigating such a place. The only con- 

 nection with the house is by two win- 

 dows. N. L. 



I cannot give size of heater, or area of 

 pipe necessary for your conservatory 

 without more dimensions. State the size 

 of each compartment and the tempera- 

 ture wanted; then I can give an intelli- 

 gent answer. 



No, it will not be safe to use hydro- 

 cyanic acid gas for fumigating such a 

 compartment unless the wdfk is done 

 when the adjoining residence is entirely 

 vacant, L. C. C. 



KELLER POTTERY CO. 



Manufacturers off Florists' Red Flower PotSy ■-. 

 Azalea Pots, Bulb and Fern Pans, Etc. 



The very best f hlppins facili i'-s on b'^th rennaylvanla R. R. snd Ph*l»dp)pbia & ReadloK R. R. 



213 TO 223 PEARL STREET, 



NORRISTOWN, PA. 



"The Way to Get There 



Is to Get There." 



The way to get pots 

 that will increase the value 

 of your plants, is to order 



Syracuse Red Pots. 

 They are as tough as can 

 be. porous as they ought 

 to be. and very light. 



Order and test. 

 Syracuse Pottery Co. 

 Syracuse, N. Y. 



Mention Tho Rfvlew when you write. 



FOR SALE.... 



New and Second-hand 



OULF CTPBB8S 



OBBBVHOnSB LITIIBBB, 



HOTBBD BASK. 



aBBEBKOUBB OLA8B, 

 BOXZiBBI, 



PZPB ABD rZTTZBOB. 

 BTBAM FITTZHa TOOLS, 



H08B ABD HOBB VALVB8, 

 VBBTILATZHO APPABATU8 



Write for our prices on anythlDg you may need 

 for the erection of your greenbouses. 



METROPOLITAN MATERIAL CO. 



QrMiihoase Wrecksrs 

 1398-1408 Metropolitan Ave., Brooklyn. N Y. 



King Coostroctioo Co. 



North Tonawanda, N. Y., and Toronto, Ont. 



New Greenhouse Catalogue 



Saady for distrilmtlon. 



SEND FOR ITI 



Mpntlnn Th» WptIpw when yog write. 



BED 8TABDABS POTS. 



Price per 1000. f. o. b. Uarrlbon: 2-ln.. tS.JS; 

 2^iD.. K70 2X-iD., tS2S: 8-in.. t4.25; SH-in. 

 15.60. 4-iD . M W: 6-in.. tll.OO; S-in., $18.00. Oaab 

 must accompany order. 



KABBIBOB POTTBBT. Barrlaon. Oblo. 



Me.itlou The Review when you write* 



Don't Fail 



To write to the 



Advance Co. 



For eatimatea on 



Ventilating Apparatus, 



Pipe Carriers, 

 Gutter Bracicets, etc. 



Richmond, Ind. 



Mpntlnn The Rpylew when yon write. 



The Standard 



Ventilating Machinery 



The origrlnal machine with 

 self-olllng cups. The most 

 powerful, least compU- 

 CHted, very i otnpact with 

 ease of operation. 



The New Duplex Gutter 



Over six miles In use and 

 birhly recommended by 

 all. The only DRIP PROOF 

 grutter on the market. 



TIN Stiidard Ittsm SIna-Trai 

 It haa no equal for simplicity 

 or its working. Cata'osne free. 



I. HIPPARD, Youngstowfl, Ohio 



Mention The Review when yon write. 



SUPERIOR 



boilers are the best boilers: get our catalogue 

 sod aik where you can see the boi er. It is 

 worth Investigating. 



BUPBBZ'^B KAOHXBB k BOX&BB WKS . 



ia9-133 W. Bnperior St., Chicago. 



Mpiitlon The Review when yon write. 



JUST A MINUTE 



^^^^ THAT 18 HOW LONG IT TAKES A 



rfWlTTBOLD.... 



IAIatering system 



to water or syrinfre your greenhouse. It will 

 p.iy yuu to Investltrate. For particulars address 



AoQis Wittbold, 1708 N. Halsted St., Chicago 



Ueotlon T&e Review when yoa write. 



