:ry 



626 



The Weekly Florists' Review* 



Jvvt 26, 190e. 



rssss 



Robber Roofing 



The origrinal flint coated. 

 Write for catalog: and samples. 



SALL MOUNTAIN ASBESTOS 



MFG. GO. ^0 '• Cinal St., CHIMBO 

 Mention The Review when yon write. 



HarK 



FURMAN BOILERS 



SAVE FUEL 



Writ* for Catalogue 



See advertisement in last week's 



Review and watch for it next week, 



THE HBBENOEEN MFG. CO., Geneva, N. T. 



Mention The Kevlcw when you write. 



High-(irade Boilers 



2S2Sio. For GREENHOUSES 



STEAM and HOT WATER 



GIBLIN&CO.,Utica,N.Y. 



Mention The Review when yon write. 



house, and a 3 -inch flow from that point 

 to the far end of the new house, will 

 undoubtedly provide the necessary heat 

 for the radiation in the plant. The new 

 house 25x100 feet will need a 3-inch 

 flow and nine 2-inch returns to maintain 

 a lettuce temperature. The only fault 

 is the length of the run from the boiler 

 through the new house, 135 feet, which 

 is too long for the best results with 

 hot -water. In your climate, however, 

 there should be no difficulty in doing 

 the work with the boiler specified. If 

 the boiler could be a little more centrally 

 located, the runs could be shortened 

 and a greater efficiency secured. 



A 2% -inch flow pipe will supply heat 

 for 600 square feet of radiation, i. e., 

 960 lineal feet of 2-inch pipe, while a 

 3-inch pipe will supply heat for 900 

 square feet of radiation, or 1,440 lineal 

 feet of 2-inch pipe. The expansion tank 

 should have fifty to sixty gallons capac- 

 ity, and should be elevated as high as 

 convenience will allow, ten or twelve feet 

 above the highest point in the heating 

 system. L. C. C. 



BOILER CAPAQTY AND PIPES. 



I have two houses each 19x50, five feet 

 to gutter, nine and one-half feet to ridge; 

 one lean-to 9x40, five feet to gutter, seven 

 feet to ridge; one house 34x60, five feet 

 to gutter and seventeen and one-half feet 

 to ridge. A dwelling house abuts on the 

 end of one of the houses 19x50. My 

 boiler room is at the opposite end of the 

 range, on the corner of the large house. 

 The latter is to be used for carnations. 

 The large house has no glass below the 

 gutter. The others are glass above three 

 and one-half feet. 



Can I heat these with a steam boiler, 

 using hot water, ten feet by thirty-six 

 inches, with twenty-eight 3-inch flues? 

 It is return flue style, and is bricked in. 

 The two houses 19x50 are piped with 

 4-inch soil pipe, and the lean-to with 

 2-inch pipe. Can I connect onto this 

 4-inch piping? How shall I arrange the 

 pipes in the house 34x60 feet? W. P. 



The boiler in question, if used as a 

 water heater, will have ample capacity 

 to provide heat for maintaining a proper 

 temperature in all of the four houses 



T 



SPRAY PUMPS AND APPUANCES 



umiqirs i.t.- 



■KMD FOR CATALOG 



Pipe Fittiflgsaoi 



PUMPS FOR EVERY PURPOSE 



THE BEST HOSE 

 ^ ^ HOSE TBIMMINGS 



FURMAN HEATING BOILER# bJ^J 



BOILERS, RADIATORS, 

 STEAM TRAPS 



Have you heard of SMQOTH"ON Iron Cement? Ask ua. 



HENION&HUBBELL, 



61-69 N. Jefferson St. 



CHICAGO 



The Largest Dealers in tland, Steam and Power Pumps and Supplies in the World. 



Mention The Review when yon #rite. 



FLORKNCB HKATKRS 



COLUMBIA HEATING CO . Belvidere. III. 



Sales Oept.. 36 Dearborn St.. CHICAGO 



Mention The Review when yoo write. 



USED BY LEADING GROWERS 



everywhere to return condensation 

 in steam pipes. With our Trap the 

 Boiler need not be set below the 

 coils. For fall information write 



MOREHEAD MFG. CO. 



1041 Grand River Ave., Detroit, lUoli. 



Always Mention the.... 



Florists* Review 



When Writing Advartleezs. 



Greenhouse Boiler. 



•I Brie street. eRICAeO.] 



Boilers made of the beat material; shell, flre-boz 

 sheets and heads of steel ; water space all around, 

 front, sides and back. Write for Information. 



Mention The Review when yoo write. 



The John Davis Co. 



Halsted, 22d and Unloa Street 



CHICAGO, ILL. 



Manutacturera and Wliolesaiers ol 



i' ( 



Wrougiit b-on Pipe 

 Cast-iron nttings 

 Valves, Pumps 

 Steam Traps 



and everything: used in a Steam Plant 



A majority of the Houses are changing 

 from water to steam. The only pipe to use 

 is the genuine Wrought Iron and "Byers" 

 is the best made. Write Us fob Prices. 



WK REFER TO 



BASSETT * WASHBURN 



POEHLHINN BEOS. CO. 



GEOBGE REINBEBO 



PETEB BEINBERG 



Mention The Review when yon write. 



