530 



The Weekly Florists' Review* 



.Tanuauv 3, 1007. 



The Whilldin Pottery Co. 



STANDARD rtOWER TOTS 



Our output ot Flower Pots is larger than any concern in the World 

 Our Stock is always Large and Complete 



Main Office and Factory. 



713 WHARTON STREET, PHILADELPHIA 



Warehouses. JERSEY CITY. N. J LONG ISLAND CITY. N Y 



Mention The Review when you write. 



.^^rnfT^ 



(wXAXa 



oXf; 



vXeXrXy 



t>Xtxr 



rMXoXj 



SX«X3y>C: 



kXiXnXd; 



IXOXd 



Greenhouse Seating. 



CONVERTING A COIL BOILER. 



('onld a box coil ]iipe boiler bi; cuii- 

 vertcil into a steam lioiler tor oreen- 

 house lieatiiig.? J. L. K. 



No. T do not tliiiik it advisable to 

 attempt to constnu't a steam boiler for 

 greenhouse heatiiiii: out of pipe coils. 

 This would be a water tube boiler which 

 would carry only a small amount of 

 water, which would make it dangerous 

 and uncertain. Water tube boilers for 

 power purpcises are not usually made in 

 sizes smaller than 150 horse-power ex- 

 cept for special uses, such as the flash 

 boilers of automobiles. L. C. C. 



PIPE FOR HEATING. 



How many runs of pipe will be re- 

 quired, what size, and how best arranged 

 to heat \Aith hot water three houses 10x8(J 

 feet, ridge and furrow plan, no center 

 walls? The outside walls are four feet 

 and fully exposed except for a shed on 

 the west end. The l)oiler is located in a 

 cellar uiuler the shed opposite tlie center 

 house. The temperature is sometimes 45 



degrees below zero. 



J. B. 



The three houses in question can be 

 piped as follows: If L'-ineh pipe is used 

 a L'lXinch flow under each ridge can be 

 nuide to feed eight L!-inch returns 

 through each house, i. e., three li^^-ineh 

 llow pipes and twenty-four 2-inch returns 

 for the entire plant. Jf the benches are 

 so disposed as to allow placing the ra- 

 diation under them it would Ix? well to 

 put one or two more jupes under the 

 ben(,-hes next to the out.'^ide walls than 

 under the others. If the piping is to be 

 hung on the outside walls and on the 

 jjosts under the middle gutters, see that 

 the heavy coils are placed on the outside 

 walls. Six pipes on each outside wall 

 will be none too much, then scatter the 

 other twelve under the benches as best 

 you can to provide the desired bottom 

 iieat. L. C. C. 



TROUBLE WITH HEATING. 



I am having trouble with my heating 

 plant. My house is 19ljxl25, three feet 

 to the eaves and nine feet to the ridge. 

 The boiler is twenty-seven inches by six 

 feet and h.as thirty-seven 1^,4-inch flues. 

 I have one 2^ '.-inch flow which rises six 



POTS OF QUALITY 



If we were to manufacture grreenhouse pots from any other kind of clay, our argument that 

 IONIA. POTS are the BEST POTS would loose its efTcct. 



I'nr 36 years the demand for them has steadily increased. Hundreds of florists use them 

 exclusively. Make up your spring order. Send it to us now. 



IONIA POTTERY CO., Ionia, Mich. 



We will ship 

 w^hen you direct. 



Monfion The lioview when yon ^^Titp. 



KELLER POTTERY CO. 



Nanutocturers off Florists' Red Flower Pots 

 Azalea Pots, Bulb and Fern Pans, Etc. 



The very best shipping facilities on both Pennsylvania R. R. and Philadelphia and Reading R. R. 



213 to 223 PEARL STREET, NORRISTOWN, PA. 



Mention The ReTlew when yoa write. 



Red Standard Pots 



Price per 1000, F. O. B. Harrison: 2-in.. $2.50; 

 2K-in., $2.95: 2>^-in., $3.50: 3-in., $4.50; 3j^-in., $5.85; 

 4-in., $7.20; 5-in., $11.70; 6-in., $19.80. Cash matt 

 accompany order. Price list for larger sizes, 

 Saucers, Fern Pans, Azalea Pots and Hanging 

 Baskets on application 



HARRISON POTTERY, Harrison, Ohio. 



Mention The ReTlew when yon write. 



Kramer's Pot Hanger 



For Sale by Wholesale Seedsmen. 

 Florists and Supply Dealers. 



Price, $1.00 per doz. by express. 

 Sample doz. by mail, $1.25. 



I. N. KRAMER & SON, Cedar Rapids, Iowa 



Mention The RcTiew when yon write. 



I'cct, then runs throuj;li the length of 

 tlic liou.se uith a gradual rise of eighteen 

 inclies. The main then branches into 

 t\vo li^.-inch pipes, each- one feeding 

 four l^o-iufh returns. The returns enter 

 a manifold tind return to the boiler 

 through tAvo li:^-inch pipes. The ex- 

 pansion tank is ten feet above the boiler 

 and connects the return close to the 

 boiler. AVould tliis boih^r be big enough 

 to heat another house the size of this 

 one? My fire-box is twenty inches in 

 diameter \Aith a rocking grate. 



J. W. H. 



You do not mention the difficulty with 

 your heating plant, but the piping of 

 the house is at fault if you are not get- 

 ting heat enough. You have about one- 

 half enough pipe in the house for a 60- 

 degree temperature and the riser should 

 be a 3-inch instead of 2i{.-inch pipe, if 

 the piping is increased. The boiler in 



ANOTHER YEAR 



Has rolled aroiiocl :in<l 

 each month more people 

 have ordered 



Syracuse Red Pots 



There's :i roason. Do 

 you know It ? One order 

 will tell. 



Syracnse Pottery Co., 

 Syracase, N. T. 



Mention The Kevlow when yon write. 



RED 



Standard Flower Pots 



Price list and samples on application. 



PADUCAH POTTERY CO., IKC. 



PADUCAH. KENTUCKY 



(|uostion has but little more than suffi- 

 cient capacity for the house it is now 

 used to heat. L. C. C. 



COLUMBUS, OHIO. 



"With regard to our Christmas busi- 

 ness, the best that I can report is that 

 we had an average volume of trade as 

 compared with past years. There were 

 several conditions which directly opposed 

 a great business. In the first place, the 

 weather could not have been worse. For 

 ten days before Christmas it snowed or 



