Mat 28. 1808. 



The Weekly Rorists' Review,* 



69 



ABOUT THE HEAT THAT GETS AWAY 



You know that the longer the fire travels, con- 

 stantly coming: in contact with the water-ways, 

 the more the heat is harnessed and the less goes 

 up chimney. So far so good— but of still greater 

 importance is the extracting or absorbing of the 

 greatest amount of beat directly In the combustion 

 chamber when the burning gases are hottest. This 

 is what is accomplished by the "Burnham" cross fire 

 channels with their side flue openings, which chan- 



nels are surrounded on three sides by extra deep 

 water-ways. The heat that these deep water-ways 

 fail to absorb is then practically all taken up by the 

 fire travel in its Journey three times the boiler's 

 length. So these are the reasons why, for green- 

 house economy, you can't beat the "Burnham" Hot 

 Water or Steam. 



Bum hard or soft coal. Send for the new boiler 

 catalog. 



Lord and Burnham CO*^ 1133 Broadway^ New York 



Boston: 

 819 Tremont Bids;. 



Philaddphia: 

 1215 Filbert Street 



Mention The Review when you write. 



55 degrees. The houses run east and 

 west, with a glass gable in the west end. 

 The boiler is under the shed at the east 

 end. How should each be piped for steam 

 and what horse-power of horizontal tu- 

 bular boiler is required! We get water 

 from a spring-pond and should like to 

 get your advice as to the water pltmt. 

 What can we do to avoid a boiler-pit f 



H.O. 



Regarding the direction and piping of 

 your houses, will say my personal prefer- 

 ence with even-span houses is that they 

 run north and south, with the work-room 

 and heating plant at the north end. 



Houses No. 1 and No. 2 should each 

 be provided with a 3-inch flow under the 

 ridge and fourteen li4-i°ch returns the 

 length of the house. Houses No. 3 and 

 No. 4 should each be provided with a 

 2%-inch flow under the ridge and ten 

 lii-inch returns, while house No. 5 

 should have a 2-inch riser under the ridge 

 and seven li4-inch returns. 



By installing a return steam trap you 

 can arrange the boiler on the level of 

 the greenhouses. This will require the 



Pipe Fittings — Imico Boilers 



FOR GRKKITHOnSK WORK 



ILLINOIS MALLEABLE IRON CO. 



5S» DIVKR8KT BOULBVARD CHICAGO. 



Mention The Review when you write. 



overhead risers as suggested, and all the 

 water of condensation will be returned 

 into a hot well, from which it can be 

 lifted to the boiler by the steam trap. 

 The water plant can be arranged by use 

 of a ram, windmill or power pump driven 

 by motor, gas engine or steam engine. I 

 am inclined to believe that either gaso- 

 line or steam power will be most satis- 

 factory. The water would be delivered 

 direct to mains or into an elevated stor- 

 age tank as desired. 



If you use a gravity system, the water 

 level in the boiler should be at least two 

 feet below the level of the lowest radi- 

 ating pipes in the houses; more would 

 be better. The boilers should have a 

 rated capacity to carry 4,000 square feet 



of radiation or more. One return tubu- 

 lar boiler, rated at forty horse-power, 

 should be sufficient to heat this plant. 



ONCINNATL 



TheMariEct 



There has been no change in the 

 state of the market. May 25 it was 

 about as poor as it was last week, and 

 were it not for the prospects of a good 

 Decoration day trade the outlook would 

 be discouraging. We are having hot 

 weather and it shows on the quality of 

 the stock. Many of the carnations ar- 

 rive badly used up. Home-grown stock, 

 and that shipped but a short distance, 



