* ' ' V .T?'* y*' -az ~^. 



74 



The Weekly Florists' Review^ 



Jdnb 10, 1909; 



STUTTLES 



Join Boiler Tubes tighter, quicker 

 and cheaper 

 than any other 

 way :: :: :: 



CLAMPS 



Sample free, you pay 

 express 



No 1—4x3 In. ^3 boiler flue reducer clamp. 

 No. 2— 4-in. cast iron pipe bub repairing 



clamp. 

 No. 8— 8x2-ln. ^ boiler flue reducer clamp. 

 No. 4— 1%-ln. boiler flue clamp. 



* 



Patented 



A size 



for every 

 purpose 



Send for Circular 



No. 5— S^fl-in. boiler flue clamp. 



No. 6— 2 in. boiler flue clamp. 



No. 7— 4in. heavy cast iron pipe clamp. 



No. 8— Special boiler flue elbow. 



No. 9— Clamp for above. 



No. 10— 4-in. boiler flue clamp. 

 No. 11— 2»fl-ln. boiler flue clamp. 

 No. 12— 8-in. boiler flue clamp. 

 No. 18-li«-in. boiler flue clamp. 



Henry Stuttle, s 



I NVENTOR AND PATENTEE 



. MUNSON, 68 N. State St, Chicago Sales Agent 



Batavia, 111. 



Mention The Review when vou write. 



feet of radiation for every 100 square 

 feet of glass, multiplied by 1.5. Divide 

 this by 125. The amount found will be 

 the grate area. Ratio of your style boiler 

 in heating surface to grate area is twenty 

 to twenty-five. G, T. E, 



PIPING TWO HOUSES. 



We want to pipe two houses, one 21x 

 100 feet and the other 27x100 feet. How 

 large pipe should we use for the flows, 

 and how many 2-inch returns do we need? 

 We will use hot \^ater. The house has 

 two feet fall to the boiler. (How deep 

 in the ground should the boiler be? We 

 want 50 degrees in zero weather. The 

 boiler is located at the north end of the 

 larger house. The houses have 5- foot 

 walls and are twelve feet to the ridge. 

 A. G. 



Kun two 3-inch flows through the mid- 

 dle of each house and under the ground 

 about a foot or so. Elbow off at the far 

 end, one to right and one to left. In the 

 21-foot house, come back with four 2-inch 

 returns on the half exposed to the 

 weather and three 2-inch returns on the 

 other side. In the 27-foot house run two 

 3-inch flows the same as in the 21-foot 

 house, with five returns on the exposed 

 side and four on the protected side. If 

 the houses are separated by a space, put 

 in one more 2-inch pipe and divide 

 evenly. 



The boiler should be down so that the 

 top of the boiler is six feet below the re- 

 turns in the greenhouses. This gives a 

 good, roomy place over the top of the 

 boiler. G. T. E. 



DENVER. 



The Market. 



Decoration day business was equal to 

 or greater than last year, prices obtained 

 being better, the sum taken being greater, 

 with perhaps less stock being handled, 

 owing to the scarcity. There being no 

 outdoor flowers of any kind, the call for 

 carnations was particularly heavy and 

 every store was completely sold out, which 

 boosted the prices. Some growers asked 

 Christmas prices, regardless of the qual- 

 ity, which may have been a mistake, as 

 some of the store men said they would 

 rather be out of them than to hold up 

 their customers for an unreasonable price. 



Roses were fairly plentiful and Beau- 

 ties were in demand, with the supply 

 about balanced. 



Take it all in all, the business done 



THE SUPERIOR 



Improved Internal Fired Boiler 



Made in ten (10) eizes. 



No brick foundations required. 



Can be cleaned while in use. 



Shipped on skids ready for installation. 



Specially designed for Greenhouse use. 



Investigate before buying. 



Catalogue and prices on application. 



Superior Machine & Boiler Worics, 



126-133 W^ Superior Street, CHICAGO, ILL. 



Mention The Review when you wnte 



\ 



For The Greenhouse 



^ MOREHEAD 



RETURN STEAM TRAPS 



The present improved Morehead Automatlo Return 

 Steam Traps are the result of twenty years' use and development io thou^aada of heatioK 

 and steam plants throag:hout the world. The "Morehead" was the Orlg;laal and ha^ at 

 all times been the Standard by which the comparative values of other traps have been 

 measured. They've stood the test for 20 years, and have gained the "urell-done" of all userH. 

 Will you join the ranks ? Cataloeue on request. 



MOREHEAD MFG. CO., |043 Grand Rinr Ave., Detroit, MiCll. 





Mention The Review when you write. 



WRITS FOR OATAIvOOCE 



eTofu^ERSl 



S55'>^yFi*»* 



U nited S tates Heaterfompany 



DETROIT, MICH. 



High-Grade Boilers 



a^KS.. For GREENHOUSES 



STEAM and HOT WATER 



GIBLIN&CO., Utica, N.Y. 



WWW Always mention the FlOTISts' RcvieW ^'licn writing advertisers. W It 



