p.'.i.'-^'' I /^ y !>* . ' T-"-.**^"*^ 



JPLX 8, 1909. 



The Weekly Florists^ RevkW. 



«7 



CLAMPS 



Sample free, you pay 

 express 



STUTTLE'S 



Join Boiler Tubes tis:hter, quiclcer 

 and cheaper 

 than any other 

 way :: :: :: 



Patented 



A size 



for every 

 purpose 



Send for Circular 



No 1— 4z8in. ifl boiler flue reducer clamp. 

 No. 2— 4-1d. cast iron pipe hub repairioK 



clamp. 

 No. 8— 8x2-ln. ^ boiler flue reducer clamp. 

 No. 4— 1%-in. boiler flue clamp. 



No. 6— 8>s-in. boiler flue clamp. 



No. 6— 2-in. boiler flue clamp. 



No. 7— 4-In. heavy cast iron pipe clamp. 



No. 8— Special boiler flue elbow. 



No. 9— Olamp for above. 



No. 10— 4-in. boiler flue clamp. 

 No. 11— 2'ii-ln. boiler flue clamp. 

 No. 12-8-in. boiler flue clamp. 

 No. 13— l^a-in. boiler flue clamp. 



Henry Stuttle, b 



I NVENTOR AND PATENTEE 



MUNSON, 68 N. State SL, Chicago Sales Agent 



Batavia, 111 



Mention The Review when vou write. 



Steam Traps 



Morehead return steam traps of 



every eize.' Special prices for immediate 

 orders for future delivery. 



Rollins Steam Specialty & Valve Co. 



486 Dearborn St., CHICAGO 



Mention The Review when vou write. 



30-foot house and eleven in the 23-foot 

 house. G. T. E. 



HOUSES AT RIGHT ANGLES. 



I am going to erect a greenhouse, 29x 

 111 feet, running north and south, for 

 carnations. It will have cement walls, 

 with three feet of glass in both sides and 

 a glass gable in the south end It will 

 join an east and west house on the north, 

 but will be exposed on both sides and at 

 the south end. It will measure fourteen 

 feet to the ridge. The furnace is under 

 the east and west house, at the south 

 side, and the smokestack is outside of it; 

 consequently the smokestack will be in- 

 side of the new house at the north end. 

 I use hot water. Please tell me how best 

 to pipe this new house. My idea is to 

 carry three flow pipes into the new house, 

 then straight up, one to the ridge and 

 one on each side under the purlins to the 

 south end, then down and back to the 

 boiler under the benches. Is 2-inch pipe 

 large enough for the flow pipes! I am 

 located in Kansas. S. M. 



Your idea is all right, only keep the 

 flows down as low as possible, as heat 

 rises and pipes above the plants are just 

 heating outdoors, so to speak, as no heat 

 gets to the plants. The 2-inch flows are 

 all right, but I would advise four instead 

 of three. Run 1*4 -inch for returns. 



G. T. E. 



TVO WISCONSIN HOUSES. 



We are about to build two connected 

 houses, each 20x93 feet. The side walls 

 will be six feet high and there will be 

 forty-two inches of glass in the south 

 side of the south house. There will be 

 two rows of pipe purlin supports in each 

 of the houses and the side posts will be 

 of pipe. We have on hand about 1,500 

 feet of 2-inch pipe, which we wish to 

 use. Other necessary pipe we can buy 

 of any size. Please tell us what size of 

 pipe to use and where to place the dif- 

 ferent runs. We heat with hot water 

 and the houses are to be used for car- 

 nations. Z. K. J. 



Use 2-inch pipes for heating pipes and 



INSTALL A 



"DETROIT" Return Trap 



AND YOU BUY A GUARANTEE 



It takes 90 to 120 lbs. of steam per horse power toloperate 

 an ordinary boiler feed pamp. "Detroit" Return Traps 

 require only about one-tenth that amount. Why not save 

 the nine-tenths ? 



Write VLB size of boiler and number of sqnare feet of glass 

 in your greenhonses, for onr proposition. 



Address DeptT.R., 



DETROIT, MICH. 



DO TOU KNOW ABOUT TUB 



Hartio Rocking Orate 



IT SAVES COAL 



MARTIN GRATE CO. '"<^r^ 



Mention The Review when you write. 



WRITE FOR OATAIX>6UB 



ep ERsi 



SiS^^?^* 



UolM S tates Heaterf.oinpaiiyi 



DBTROrr. MICH. 



Mention The Review when you write. 



3-inch for the main flow and returns. 

 Run a 3-inch flow pipe up through under- 

 ground to the far end. Tee off with five 

 pipes on each side and rise to the heat- 

 ing pipes under the benches; bring tuese 



EMERGENCY PIPE GUMPS 



To repair splits 

 and rust holes 

 on pipe. Made 

 of malleable 

 iron, and guar- 

 anteed to stop 

 the leaks. 



Send for cat- 

 alogue of 

 Pip* Repairs »nd Staam Spaoialtlas 



JAMES McCREA St CO^ 



Maaufaoturers 

 •1 -63 W. Watkington St. , CHICAGO 



Mention The Review when you write. 



