OCTOBBB 31, 1912. 



The Florists' Review 



93 



TRAVIS GREENHOUSE ROCKER GRATE 



The Orates that chew moru 

 cinders than can accumulate 

 with the hardest flrlng. Ask 

 the man who uses them. We 

 guarantee that, if you have 14 

 inches of ashes and cinders, 

 and four inches of fire on top. 

 you can shake the trrate and 

 all will settle down, the Hre 

 remaininff on top and sroinir 

 thiouffh last. Ask for a li^t of 

 ust-rs. Write to them and re- 

 ceive their personal opinion 

 of the kind of service received 

 from the Travis Grates. 



For prices, give tlie size of your furnace 



G. E. TRAVIS COMPANY, 



HENRY, ILL., V. S. A. 



Mention The Bevlaw when yog write. 



Christmas 

 Present 



GET ONE FOR YOUR BOILER [ 



Piping Qttts Hotter 



We have one of your special greenhouse 

 Generators, and it does the work in a very 

 satisfactory manner. We have noticed 

 that the returns are much hotter than 

 they were with the old gravity system. 

 We intend to install Generators on all our 

 heating systems the coming season. 

 J. D. Cockcroft, Northport, L. I.. N. Y. 



Th« Kroaschall Q«n«rator— It 

 •p««ds up circulation 



Kroeschell Bros. Go. 



444 W. Erie Street 

 CHICAGO, ILL. 



, Mention Th» lt»Ti>w wh.B too writ. - 



neath if raised benches are used in the 

 house. Kun all of the flow pipes down- 

 hill and connect the expansion tank at 

 the highest point. 



GREENHOUSE AND BESIDENCE. 



Will you please give me a plan for 

 the heating of my greenhouse? It is 

 •55x100 and fourteen feet to the ridge, 

 with no glass in the sides. The walls 

 ■ire concrete. The house is built 

 against the dwelling house, with half 

 of the gable exposed. A coal shed at 

 the west also protects half of the west 

 ^'able. I should like to know how td 

 l^ipe the house and what size of . boiler 

 to use to heat it with hot water to a 

 femperatuTp of 60 degrees^in this Ohic) 

 •Hmate. t also Want tb"' heat three 



4t 



-rX^ 



RETURN TRAPS 



insure a more uniform tem- 

 perature in the houses by 

 keeping all steam lines free 

 and clear of condensation. 



Sluggish lines sap the real 

 heat value out of the new 

 steam and add dangerously 

 to the general inefficiency 

 of the plant. 



Avoid this condition in 

 your system by installing 

 a "Detroit" Return Trap. 



Bulletin No. 326- WF gives details of construction, operation 

 and application of Detroit Traps. Yours upon request. 



If you would like the co-operation of our Steam Trap Department in the 

 selection of the proper size " Detroit " Trap for your requirements, write us. 



American BlowerGompany 



•^— — DETROIT. MICM. ■ 



U. S. A. 



Canadian Sirocco Company, Windsor, Ontario. Manufacturers for Canada. 

 Mention The ReTlew when 70a write. 



Ford & Kendig Co. 



"SfeDemri" Wwufct fy 



Bapedally adapted for OrMnhonse Work. Tl% 

 tines, Vftlres. Tool*, etc. 



24tli ud Wn4 StL niILADELnflA.rA 



Mention The KeTlew when you write. 



DO TOU KNOW ABOUT THS 



Nartm Rocking Gnte 



IT SAVES COAL 



MMtTIN GRATE CO.,"' J£sagr •*• 



rooms on the first floor of the dwelling. 

 The greenhouse is new. M. M. T. 



As nearly as can be determined from 

 the description given, it will be pos- 

 sible to heat the greenhouse 35x100 

 feet by using five 214-inch flow pipes 

 and fifteen 2-inch retu-ns.. Eun one 

 flow under the rid^e, one on each wall 

 plate and the others under the purlins. 

 Three or four of the returns can be 

 under ej^cji side bench or on the walls, 

 and tile* others iiuder'th^ otTier benches, 



Sale* Off tcew ; 



New fork 

 Boa ton 

 Philadelphia 

 Chleaffo 



Lord & Burnham Co. 



Factorlen : 



Irvington, - N. Y. 

 Des Plaines, - III. 



Mention The Beview when you write. 



Sinonds Heating & Specialty Ci. 



Grand Rapids, IMIch. 

 GREENHOUSE 



ONE POUND PRESSURE 



VACUUM HBATINO SYSTEMS 



Always f&eodon the Floclits' Rrview when 

 vrftin^r advcrtiien. 



