70 



The Weekly Florists^ Review* 



August 25, 1910. 



BUY THE 



Taylor Automatic 

 RETURN TRAP 



,/7?r'./^-- 



Exhaust Tkln 

 Adjuitment 



ClMU out Plug 



Staualote 



AND SAVE MONEY 



Write for our Guarantee 

 and Best Prices 



TAYLOR STEAM SPECIALTY CO. 



BAHLE CREEK. MICH^ U. S. A. 



Mention The Review when >uu write. 



THE DIVIDED SEQION BOILBtS 



GAPffltERS 



EasT to Set Up. Easr to Operate. 



Write for Catalogue. 



UNITED STATES RADIATOR CORPORATION 



Nam Offket. DUNKIRK. N. T. BrMckts !■ all laria cHiei 



Mention The Review wlien you write. 



temperature? I wish to use a bed in 

 the lean-to for rooting cuttings. I will 

 install a No. 2 Kroeschell boiler this 

 year. K A. M. 



To heat the house 28x44 feet, with 

 eight and one-half feet of glass in the 

 walls, it would be best to use three 

 2V2-inch mains and fifteen 2-inch re- 

 turns, but as the 3-inch flow is now in 

 use, it will answer if two additional 

 2^-inch mains are put in and the re- 

 turns are divided between the flows. 



For the proposed lean-to, 8x30 feet, 

 use one 2-inch flow and four 2-inch re- 

 turns. In the potting shed, 14x24 feet, 

 use one 2i^-inch flow and four 2-inch 

 returns, 



CHANGING BOILEBS. 



I intend to make a change in my 

 boilers and should like to know if I can 

 use one boiler in place of the three I 

 have at present. 



We have three houses, each 24x85 

 feet, all connected under the gutters, 

 'which are seven and one-half feet high. 

 The ridges are fifteen tpet high. We 

 also have one house at the end of these, 

 20x150 feet and fifteen feet to the 

 ridge, with a 5-foot wooden wall on the 

 outside; also two houses, each 18x75 

 feet and eleven feet to the ridge, with 

 4% -foot wooden walls. The boilers are 

 in the workshed at the ends of these 

 houses. 



At present we have the following 

 piping in use in these houses: 2,600 

 lineal feet of 4-inch pipe, 300 feet of 

 21^-inch, 1,900 feet of 2-inch and 2,100 

 feet of 1^-inch. This heats our green- 

 houses satisfactorily. 



We are using one cast-iron sectional 

 boiler with a grate 30x30 inches, one 

 with a grate 30x42 inches and one with 

 a grate 24x30 inches. This last boiler 

 is cracked and so we want to put in a 

 large boiler in place of all the others. 

 There is just twenty square feet of 



THE KITTS 

 Improved Hydraulic Damper Regulator 



IS. 



A MONEY 

 SAVER 



Whtn overhauling for the winter why not 

 install one and save money ? Now is the 

 time to order. Write for full particulars. 



KITTS MANUFACTURING CO 



OSWEGO, NEW YORK 



aientlop The Review when you write 



The MOREHEAD 



BOILER FEED 



Sent on 30 Days' 

 Free Trial. 



CUBSTITUTE a Morehead "Boiler Feed" Trap 

 ^ for your steam pump and save 90^o of the steam 

 necessary to operate a pump. Steam pumps, handling 

 hot water, stick, short stroke and act badly. Morehead 

 " Boiler Feed " Traps do not. 



Our " Trap Book " will thoroughly post yoti. 



Send for copy — also state your conditions and we 

 will submit a complete proposal, gratis - no obligations. 



MOREHEAD MFG. CO., DepL'M/' Detroit, Mich. 



Mention The Review when you write. 



m. » > Succesaorn'to'the 

 Johu Davis Company 



No lost from sudden drops in 

 temperature if you use the 



Hughsbn Regulating Valve 



In connection with a steam heating plant. Carry 40 or 

 50 pounds pressure on the boiler and set the valve for 5 

 or 10 pounds— it will do the rest You'll be free from 

 worry next winter, if you follow this advice: " Install a 

 HuKhson ReKOlatlns Valve when making your 

 repairs." Ask for our Catalogue, which also shows 

 Stf am Traps and other devices. 



HUGHSON STEAM SPECIALTY CO. 



5021-5023 S. State St., CHICAGO, ILL. 



Mention The Review when you write. 



44 



rORD & KENDIG CO. 



Spellerized '' Wrought Pipe 



Sspecially Adapted For 



GREENHOUSE WORK 



Fittings, Valves, Tools, Etc. 

 1428-30-32 Cailowhill St., PHILADELPHIA, PA. 



Mention The Review when you write. 



