86 



The Weekly Florists' Review. 



Januakv '2o, 1912. 



Where There Is Condensation 



— there is need for a Morehead Steam Trap. Condensation in 

 steam lines is akin to matter out of place — means wasted energy. 

 If your lines are sluggish — if your houses are not of uniform 

 temperature, write us. We guarantee to drain your lines per- 

 fectly — return the pure, hot condensation to your boiler without 

 pump or injector or make no charge for the trial. Obey that 

 impulse — write now. 



Morehead Manufacturing Company 



New York 

 Chieagro 



Wichita, Kan. 

 New Orleans. La. 



Dept. "M," DETROIT, MICHIQAN 



stocks Carried in 



Pliiladelphia Memphis, Tenn. 



Birmingham, Ala. Los Angeles 



Chatham, Ontario 

 San Francisco 



J) 



"MncM-t Avitli a coil of six 2-inch ])ipcs 

 oil Tlie south side of tiie doorway; tliese 

 I'ijM- •^liould be carried arouud ou the 

 -oiiTl, ;iii(l ^vc.st sides of the house to 

 Ml.' imrtliwcst corner; ^vhcre they 

 -IhMiM lir ( (iiinected witli the heater 

 'v^ iiM'.-iii- ui: a 2J/{>-inch main re- 

 'iiiii |.i|.(. .\jiother 2i/l>-iuch How pipe 

 -li'iiiJd .lio)i down on the north side uf 

 ilii' diior and connect with a coil of five 



"I -i\ L'-inch pipes, whicli should run 

 ■ iiMiind To a iioiiit opposite the heater, 

 \\l:i I' ihey should be connected in the 

 -anic way as the icturn from the other 



oii. ir the pijics all run downhill, 

 ilicrc will In.' )i(p occasion fur usintr air 

 •.alvc^. 



If. ini- any reason, tlie main How pipe 

 ran not Ite carried up to the height de- 

 -ireil until after it has entered the 

 grceiiiiiMi-e. the connection with the 

 i'Nl'aii:>i(ui tank should still be niaile at 

 The iiiyiioT ]K)int of the system, and al- 

 though :in I'levatiou of ten feet or more 

 will be desirable, if necessary the tank 

 '■.■111 I !■ .■iiiiii.'cted direi-tlv with the flow 

 pi]..-. 



ISiOT ENOUGH RADIATION. 



I :'iii huil.JMij: a yrceiihouse. 2Jx.jU, 

 /uiiiiin- iKirth and s.uith. live feet high 

 'II til.' .ax."^ an. I .deven feet to the 

 ri.lm'. I'lca>i' let nic know the best 

 way T.. lun the pi]>es for hot water, to 

 have a teiiijierature of '>'* degrees at 

 night. There will be four benches in 

 the h'Uise. If I place two 2-inch Hows 

 under the ridge, run them to the front, 

 then drop them down and connect with 

 I'l-UU' ]^, )-in.-li ri'turns, whii^h would be 

 under the benches and would enter a 

 -'-inch return to the boiler, would that 

 bo satisfactory? I shall 

 boiler. 7 .■nn located in 



airaiigeiiient 



use a 



7 ester n Pennsvh ania. 



Wilki 



11. P. 8. 



The jdan jiroposed will not supply 

 rnough radiating surface, and larger 

 return pipes should be used, unless a 

 .'irculator is attached to the system. 

 For an open-tank system use one 2'^- 

 inch overhead flow l»ipe and ten lij-inch 

 returns, and connect the coils to the 

 heater either with one 2VL'-inch or two 

 2-inch returns. One of the returns can 

 }je on each of the plates and two 

 un.le)' each bench. Tlier(> is no [lartbu- 

 lar objection to the use of two 2-inch 

 ilow pipes, except that one 2i,{; inch 

 l'i|)e will give as good results an. I will 

 !'.■ (■liea]»er to install. 



A Steady 

 Pressure 



will always 

 be main- 

 tained in 

 your steam pipes, no matter 

 how the pressure at the boiler 

 (iuctuates, if you equip your 

 main lines with these valves. 

 Carry 40 or 50 pounds pressure 

 on the boiler, set tlie 



Hughson 

 Regulating Valve 



to carry •") or In pounds on the 

 line and you will always have a 

 reserve in ease of a sudden drop 

 in temperature. This valve 

 saves both fuel and worry. Ask 

 for catalogue and particulars. 



Hughson Steam Specialty Co. 

 S021-3 S. State St., Chicago 



50% SAVED 



Pipes, Flues 



and casing thoroughly overhauled and guaran- 

 teed. Greenhouse fittings of every description, 



ILLINOIS PIPE & MFG. CO. 



S115 8. Jaffnrnon Utrmtkt. rTr-rr-Ann 



Ford & Kendig Co. 



"Spellerized" Wrought Fipt 



Kspecially adapted for Qreenhous'^ Work, Fit« 

 tings. Valves, Tools, etc. 



24th and Wood Sts. PHUADELPfflA. PA. 



HIGH-GRADE BOILERS 



For GREENHOUSES 



STEAM and HOT WATER 



Get Our 

 Catalugue 



What's This? 



GIBLIN 8 CO., 



100 Broad Street, 

 UTICA, N. Y. 



IT'S THE NEW 



PERFECTION 



FLUE CLEANER 



and we want to send it to you for 

 30 days' FREE trial. 



The I'erfeetion will (dean welded 

 flues as well as okl ones; remove 

 scale from tubes without cutting 

 metal ; dean hot or cold flues with- 

 out changing temper; can be oper- 

 ated by tiexihle handle. 



The knives are always sharp. 

 Heads are drop steel forgings. 

 Hundreds now in use by florists. 



ScuUy Steel & Iron Co. 



Ashland Aye. and 24th St., Chicago, UI. 



WRITE TO 



Geo. B. Limbert & Co. 



557 fulton St, CHICAGO 



For Prices on 



Genuine 

 Wrought Iron Pipe 



Ask For Cataloerue. 



