KKBHlAltV .'.. low. 



The Florists' Review 



107 



TIE PERFECTIOR 



FLUE CLEANER 



C Thoroughly cleans tubes with 

 Welded ends as well as Whole 

 Tubes without cutting metal. 



a Cleans Hot or Cold tubes without 

 changing temper. 



KNIVES ARE CONCAVED 

 KNIVES ARE BEVELED 

 KNIVES ARE ALWAYS SHARP 

 HEADS ARE DROP FORCED 



Sent on 30 Days' Trial 



Writ* for Prlc«s 



Scully Steel & Iron Co., 



CHICACO • NEW YORK 



Mention The Reylew when yon ^tWte. 



G. E. TRATIS CO., HENRT. ILL. 



Mpptlon The Rerlpw when yon write. 



Full Weight "Reading" 



Wrought Iron Pipe 



Sizes >^-in. to 12-in. from stock 



FORD & KENDIGXO. 



PHMDELPHIA, PA. 



27 North 1th St. 

 S4th and Wood Sts. 



Mention The ReTlew when yon write 



the houses with the boiler, using two 

 •J%-inch pipes to join the mains to 

 the coils in each house. 



While two 21/j-inch flow pipds in the 

 detached house, 20x112, can be con- 

 nected with the 21/^-inch main which 

 leads to the boiler, they will not be 

 much more effectual as flow pipes than 

 the two 2-inch pipes, but will furnish 

 slightly more radiating surface. Un- 

 less a generator is used, I would con- 

 sider it advisable to run a 3-inch main 

 to the boiler, in which case two 2^- 

 inch flow pipes could and should be 

 used as overhead flow pipes in the 

 house. Unless it is possible to ream 

 out the opening in the boiler to admit 

 the 3-inch flow, it will answer if the 

 present opening is used. 



In the house 20x112, I would use six 

 2-inch retarns in additioi^ to the two 

 2% -inch flow pipes. The lean-to propa- 

 gating house can be heated by means 







Rather Important 



A rather important change has 

 been made at James McCrea & 

 Co M. B. Skinner & Co. have 

 taken the exclusive agency for 

 their Pipe Repairs and other 

 specialties, and, with increased 

 facilities, are prepared to give 



better service than ever. 



Have you our catalogue? Do 

 you realize what it means to you 

 to be able to repair a leak the 

 day it appears on the pipe line ? 



Anyway— write us. 



M. B. Skinner & Co. 



558-562 Washington Boul., Chicago 



Mention The Review when yon write. 



IMICO 



Hot Water Boilers 



Made by 



jllinois Malleable Iron Co. 



1801-1825 Diversey Boulevard 



CHICAGO 



Ar« NotAd for coal aconomy and goo4' 

 raaulta sanarally 



SEND FOR CATALOGUE 



Mention The Review when yon write. 



BOILER FLUES 



We make a specialty of handling carefully selected 

 Boiler Fines. 4-lnch diameter and other sizes for 

 rreenhouse piping. Gutter Posts, etc. Also, we 

 make a specialty of flues for retabing boilers. All 

 Ones are thoroughly cleaned and trimmed, ready 

 for use. General Sales Agents for Stuttle's Patent 

 Olamp and Elbow for Joining flues— no packing, no 

 leaks. New standard pipe and all kinds of green- 

 house fittings. Right prices and prompt shipment. 



H. MUN80N 



140S Wells St. Phone North 672 Chloaco 

 Mentloif The Review when yon write. 



of two 2-inch returns, which can be 

 handled if a 3-inch flow and a return 

 of the same size are used. 



PIPING IN OREQON. 



Will you please tell me how much 

 piping will be needed for a house, or 

 two parallel houses, with a total size of 

 30x175 feet? I have a Kewanee No. 5 

 fire-box boiler, for steam. The lowest 

 outside temperature known in this part 

 of Oregon is 15 degrees above zero. I 



WILKS 



Hot Water Boilers 



ARE THE MOST ECONOMICAL 

 BOILERS rOR GREENHOUSES 



Na Nlsht FIraman Raqulrad with aur 



SELF-FEEDING 

 HOT WATER BOILERS 



Send for Catalogue and prices. 



S. WILKS MFG. CO. 



3823 Shialds Ava.. CHICAGO 



WROUCHT IRON PIPE FOitSALE 



Bethreaded, thoroughly overhauled, 14 ft. and up, 



guaranteed free from splits or holes. 



It wUl pay you to correspond with oa. 



ALBERT Jk DAVIDSON 

 n7-23 Mm ««MHM. BIOOKLTN. NEW TMR 

 Mention Tba B.Tlew wh»n yon wtltc. 



want a night temperature of 60 degrees 

 in the main house, which is 22x175, run- 

 ning north and south. It is seven feet 



