.1 ' 



Mabch 10, 1914. 



^The Florists* Review 



115 



CAREFULLY 



BOILER FLUES 



SELECTED 



^ STUTTLE 

 4-inch Patent Clamp 



We make a specialty of handling carefully selected Boiler Flues, 4-inch 

 Vdiameter and other sizes for greenhouse piping, Gutter Posts, etc. Also we 

 make a specialty of flues for retubing boilers. All flues are thoroughly 

 cleaned inside and out, trimmed, and are ready for use. General sales 

 agents for Stuttle's Patent Clamp for joining flues— no packing, no leaks. 

 New Standard Pipe and all kinds of Greenhouse Fittings. Right prices 

 and prompt shipment. 



H. MUNSON, 140S Wdls St, CHICAGO 



Telephone Superior 572 



STUTTLE 

 4-inch Patent Elbow 



Mention The RcTlew when yon write. 



"The Superior 

 Boiler" 



Tor Greenhouse Heating 



Superior Ntchine & Bofler Works 



840-850 W. Superior Stroot 

 CHICAQO 



Mention The Rerlew when yon write. 



of it — to carry 600 feet of radiation! 

 The boiler is enclosed in a covering 

 about one inch thick, but none of the 

 piping is covered. What shall I dof I 

 can put a thicker covering on the boiler, 

 cover the pipes in the cellar and extend 

 the chimney with iron pipe, so as to 

 make it from five to eight feet higher. 

 I do not wish to add new sections this 

 winter and I do not intend to put in a 

 new boiler. Any necessary changes 

 must be made immediately. If you can 

 give me any more advice, I shall greatly 

 appreciate the favor. L. W. B. 



The riloses in question, I understand, 

 are 16x40 feet and ten feet to the 

 ridge. The inquirer, also makes the 

 statement, among some other memor- 

 anda enclosed with his letter, that in 

 one house, where there are 264 square 

 feet of radiating surface, the tenipera- 

 ture drops to 30 degrees in zero nights, 

 and in the other house, which contains 

 292 square feet of radiation, not over 

 40 degrees can be maintained. If the 

 houses have tight roofs and warm walls, 

 it should be possible, with this radia- 

 tion, to maintain 50 degrees in one 

 house and 55 degrees in the other, and 

 a boiler rated at 800 square feet should 

 do the work easily. Of course the pro- 

 portion between the grate area and the 



IMICO 



Hot Water Boller» 



Made by 



Illinois Malleable Iron Co. 



180M825 Oivcney Boaievard 



CHICAQO 



Ar« Not*d for coal •conemy and «••# 

 rasults sanarally 



SEND FOR CATALOGUE 



Mention The Rtrlew when yon write. 



4-INCH 



BOILER TUBES, 01 



cants par foot. 

 Naw and S. H. PIpa. All SIzaa. 



Tell us your wants. 

 nXXMOIS PIPK Ac MVG. CO. 



ai7 8. Jelienen street, CHICAGO. ILL. 



ICentton Ttie BeTlew when yoa write. 



EMERGENCY PIPE CLAMPS 



Stop any split 

 or rust hole leak 

 —permanently. 

 M. B. Skinn«r 

 & Co. 



558-562 WathiaitM II: 

 CMICAOO. ILLINOIS 



Mention Tbe Rerlew when yon write. 



