OCTOBEll 5, 1911. 



The Weekly Florists' Review, 



Where There Is Coodensatioo 



— there is need for a Morehead Steam Trap. Condensation in 

 steam lines is akin to matter out. of place — means wasted energy. 

 If your lines are sluggieh — if your houses are not of uniform 

 temperature, write us. We guarantee to drain your lines per- 

 fectly — return the pure, hot condensation to your boiler without 

 pump or. injector or make no charge for the trial. Obey that 

 impulsei— write now. 



Morehead Manufacturing Company 



Dept. 



*'M," DETROIT. MICHIQAN 



stock! Carried In 



New York 

 Cbicago 



Wichita. Kan. 

 Ntjw Orleans, La 



Philadelphia 

 Birmingham, Ala. 



Memphis. Tenn, 

 Los Angeles 



Chatham, Ontario 

 San Francisco 



i) 



Mention The Review when von write 



200r< 







Our sales to Florists for 1910 were 200>i in- 

 crease oyer 1909 and every customer satisfied. 



RETURN TRAP 



CkuoutFloi 



StMaUl* 



Taylor Steam Specialty Co. 



BAHLE CREtK, MICH. 



Write Department F, for new catalogue. 



MentloD The Review when you write 



needed to maintain a temperature of 

 60 degrees in zero weather in the two 

 houses, and about forty square feet or 

 seventy linear feet of 2-inch pipe will 

 be needed in the heater. For radiation, 

 use three 2-inch flowa and twelve 2-inch 

 returns in each house, placing one flow 

 on each wall, and the other under the 

 ridge. The returns can be arranged in 

 three coils underneath the flows. 



A LEAN-TO FOE LETTUCE. 



Please tell us how to pipe a lean-to 

 house, 12x100, for lettuce, using 2-inch 

 pipe for flowa and returns. We will 

 attach the lean-to to our present house, 

 removing the side boards and glass. 

 What effect will the pipes beneath the 

 benches in the neighboring houses have 

 on the atmosphere of the new house? 

 How manv returns will be needed for 

 each 2-inch flow. Our location is west- 

 ern Pennsylvania. W. F. C. 



In a house such as described a tem- 

 perature of 50 to 55 degrees can be se- 

 cured by using two 2-inch flow pipes 

 and four 2-inch returns. Unless the 

 heater is below the level of the returns, 

 however, it would be better to use one 

 2^-inch flow and five 2-inch returns. 

 The flow should be near the ridge and 



SPECIMEN PUNS 



FOR A 



Modern Heating System 



are given in the new 

 1911 



catalogue of all steel 



Waks Hot Water Boilers 



The self-feeding fea- 

 ture keeps an even and 

 continuous fire for 12 

 hours and longer with- 

 out any attention. 

 This makes night 

 firings unnecessary 



Write today for Your Copy of Our 

 Catalogue. It's Free. 



S. WILKS MFG. CO., 



8688 Shields Avenue, 

 CHICAGO 



IMICO 



Hot Water Boilers 



Made by 



ILLINOIS MALLEABLE IRON CO. 



1801-1825 Diversey Boulevard 



CHICAGO 



Are noted for coal economy and 

 irood results a^enerallj 

 SKMD FOR CATALOCniS 



BOILER FLUES 



4-lnch and other sizes, cleaned and trimmed 

 teady for heating, retubinff boilers or gutter 

 posts. Prices right. Also sales agent for Stattle'? 

 Patent Clamp for loinlng flues. 



H. 7«IUNSON 



1405 WeUs St., CHICAGO, ILL. 



Telephone North titH 



We have genuine wrought iron pipe 



and T' quality valves 



and fittings. 



WHETSTONE S CO. 



911 nibert Street. 



PHILADCLPUIA, PA. 



II -^_-l- •A.-i-(-r., ■«:«. 



