86 



TheWeckly Florists' RevJew. 



October 12, 1911. 



CpB CCB CCB CCB CCB CCB CCB CCB CCB CC9 CCB CCB CCB CCB CQB COB 



QUALITY 



PROMPT SHIPMENT 



PREPARATION 



tOOVHONTAS" 

 JSMOKELESSl 



C. C. B. POCAHONTAS SMOKELESS COAL ' 



The unqualified favorite of leading floriflta for twenty years. 



MAJESTIC 



A blocky splint coal. Intense, uniform and lastine heat. Minimum imparities, CArrif6 

 a lower freight rate than Pocahontas. A trial car brings a permanent customer. 



CASTNER, CURRAN & BULLITT, Inc., '^^SS&r CHICAGO, ILL. g 



CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB B 



Itentioo Tbe Raview when tou write 



i 



I 



C 

 C 



SMITH, UNEAWEAVER& CO. 



COAL 



Aathneite, Mtaadnoat, Coke tmi Gm Ooal 



TrS^^^f, Philadelphia 



Mention Tfae Review wl>en you write. 



Greenhouse Heating. 



HEAf FOB SASH HOUSE. 



We int'end opening a store in a neigh- 

 boring town and will build a house of 

 sash for plants, twenty-four feet long, 

 ten feet six inches wide, four feet six 

 inches high at the gutter and seven 

 f«et six inches high at the ridge. We 

 intend heating it by running one 1%- 

 inch How pipe along each side wall, 

 then looping at the rear and connect- 

 iag with three 1^-inch returns under 

 ■each bench, the house to contain two 

 benches. Would this be sufficient radi- 

 ation to heat it to about 50 degrees and 

 would a tank heater rated at 160 

 sauare feet of radiation and capable 

 of supplying 200 gallons of hot water 

 d« the work? W. H. 



As only seventy-five square feet of 

 eradiation will be required to heat the 

 h«use described, the heater should be 

 amply large for the purpose. If the 

 heater can be placed below the level of 

 the returns one IV^-inch overhead How 

 and six 1 14 -inch returns should be 

 ample to maintain a temperature of 

 50 degrees. 



TWO ILLINOIS HOUSES. 



We are building twp greenhouses 

 eaeh 28x150 feet, running east and 

 ■west, on a slope toward the south. The 

 north wall will be six feet high, of 

 solid concrete blocks. The south wall 

 will have three feet of concrete blocks 

 and thirty inches of glass. The divid- 

 ing wall will be of wood and an iron 

 , gutter will be used. The elevation 

 from the south wall of the lower house 

 to the north wall of the upper house 

 is seventeen feet in fifty-six feet, as 

 the houses will be connected. The lower 

 house will have solid beds and the 

 upper house raised benches. Both 

 .gables will have glass. The houses will 

 be heated by a Furman boiler rated to 

 heat 11,500 square feet. Hot water will 

 be the heating medium. The boiler 

 shed will be located on the southwest 

 corner. The maximum temperature re- 

 quired will be 60 degrees in zero weath- 

 -er for both.hoyees and we would like 

 to know tb« best way to pipe the 



=B3= 



Greenhouse Heating 



^' "^"^.Ssrand Save 20% to 50 9"^ of Coal 



Use our AUTOMATIC ELECTRIC CONDENSATION PUMP 



EVIBENCE : 



Writ. 



Catalogue 



Results 

 Count Z 



Wm. Swinbank 



FLORIST 



"clJfnxiWBkCfiokAL dsiioii' 



nANTS. aULBM jntb OOLO ftSH. 





MXf WUT «YCAM9«C VTKCfT 



•YCAMOm. lU... 



AUS. 7t)l. 



South ParK'Jlorai Co., 



Hew Caatle^TIna, ■ • 



Oentleiien:- 



I stiould lUcflTto make a little la^ulrywlth 

 rof^ra to the cnicago Pump Co .« Automatic Electric Conden«-) 

 ation PUK.p. 



Has It given aatlsfactlonT 



Co you think It ha« savefl any on the amount 

 of coal consuwedT 



About how MUCH la your electric mil per 

 laonth to run ItT 



\I8 It more economical than a trapT 



Thanking you In afiyaxice for your reply. 



Beapectfuily, 



ff« tu« It oa S40,000 fMt of fiMMU. Coat« 

 ■bout Ifi.OO to ta.OO par nontta for •lootrloltr. lUkra 

 ■ort •*•(! hMt( on lowtr jtmiv* Mmn trfm and t«k«a,' 

 40^ lose boil«r o*i»oit7. It's a aueoaaa. 

 SOUTH PABS 00. 



CHICAGO rUHP CO., 10S9 Foltra St., CHICAGO, lU. 



Menaon Tne Beview wben you wnte. 



TImUkr 



01 ne... 



L 



Bnec«<Miont to the 

 John Davis Company 



floghson Regnbtmg Valve 



are all satisfled with the results it has siven, and many 

 duplicate riders is the proof. This ValT« ^rlU znaln- 

 taUl a At^ady Vfmmvix* on the low side, no matter 

 how the inhial pressure fluctuates. By carrying 40 or 50 

 pounds pressure on the boiler and setting the valve to 

 carry 6 or 10 pounds on the line, you always have a 

 reserve to fall back on in rase of a sudden drop in tem- 

 perature. Our ■a«w oataJoKue la }uat out and if 

 you contemplate making any cuanges you had better 

 get one— it ia yours for tbe asUng. 



We Also Make Traps ttad Other DeTloes. 



HUGHSON STEAM SPECIALTY CO. 



5021-503S 8. State Street, CHICAGO 



Mention The Review when you write. 



