-TTrjfKi* fym^jiVjjiv ■ Vf,j^'V'r^'^_jii^,'irfy?*ii^y^^iFw^ 



86 



The Weekly Florists' Review* 



OCTOBEB 19, 1911. 



n'. 



Where There Is Condensatioa 



— there is need for a Morehead Steam Trap. Condensation in 

 steam lines is akin to matter out of place — means wasted energy. 

 If your lines are sluggish — if your houses are not of uniform 

 temperature, write us. We guarantee to drain your lines per- 

 fectly — refurn the pure, hot condensation to your boiler without 

 pump or injector or make no charge for the trial. Obey that 

 impulse — write now. 



^ 



Morehead Manufacturing Company 



New York 

 Gbicaffo 



Vii^ liii 



Wichito. Kan. 

 New Orleans, La 



Dept. "M." DETROIT, MICHIQAN 



stock! Carried In 



Philadelphia Memphis, Tenn. 



BirminKbam, Ala. Los Angeles 



Chatham. Ontario 

 San Francisco 



<f— ^ 



Jj 



Mention The Review when von write 



the west house is four feet above the 

 ground. This side is well protected by 

 an orchard. 



I have a 7-section boiler with a fire- 

 box that is 20x2(6 inches. Beginnii;ig 

 at the east side the bouses are^^Huk- 

 bered from one to six. The boiler iff 

 at the north end of house number four. 

 Two 3-inch flows are carried each way 

 across the ends of the houses. (The 

 inquiry gives a long description of the 

 arrangement of the present piping, but 

 the information \s so vague that it is 

 impossible to make it clear to the read- 

 ers. Therefore the correct method of 

 piping is given in the answer and no 

 attention is paid to present arrange- 

 ments.) 



Do you think I can get 55 degrees 

 in zero weather, or 48 degrees when it 

 is 10 degrees below zero outside? 



S. K. 



The description given of the piping 

 is not clear, especially that of the pip- 

 ing in the three houses on the east side 

 of the range. It is evident that there 

 are six houses, fifty-six feet long and 

 from ten to fourteen feet wide, with 

 the ridges nine feet high. These are 

 to be heated to 55 degrees in zero 

 weather. The boiler is at the north 

 end of the middle house and from it 

 two 3-inch flow pipes are carried either 

 way across the ends of the houses. 



In the houses which are ten feet wide 

 there should be one 2-inch flow pipe 

 and four 2-inch returns. If any of the 

 houses are twelve feet wide it would 

 be well to have two 2-inch flows with 

 two returns connected to each, and in 

 houses fourteen feet wide use two flows 

 and five returns. 



The boiler should be large enough 

 to handle about 1,500 square feet of 

 radiating surface. 



Nashua, N. H. — Aretas B. Chandler 

 has left his position at the store of W. 

 W. Powers. 



Wacrner Plant Boxes are 



the best and cheapest in the 

 market for Palms, Boxwood, 

 Bay Trees, etc. Ther are attract- 

 ive in desigrn. strong and dara- 

 ble. suitable for either indoor or 

 outdoor use. Made of cypress, 

 which Klves them a lastlnsr qual- 

 ity. We manufacture various 

 styles and sizes. Write for prices. 



WaONKB PaBK CONBKBVATOBIXa 



Sidney, Oliio 

 Mention The Review when you write 



Quick Budding and 

 I - mi steins 



Get into the market with bette?, 

 blooms — Sheep's Head Brand of Pul- 

 verized Sheep Manure will prove a 

 money maker for you. Unsurpassed 

 as an extra stimulant to plants, pots 

 or beds. Will not cause black spot 

 like stable manure. Free from weed 

 seeds — always ready. 

 Carnations, roses, chrysanthemtmis and violets 

 are particularly beneflted. Seud for booklet, 



"Fertile Facts" 



It shows yoa ttie dollars and cents view and 

 points out the actual profits 

 from nsine ' Slieep's Head 

 lirand, ana shows yon how 

 to prepare soils so that they 

 A wUl retain soluble plant 

 W foods near the surface of 

 "* the ground within reach 

 ot the rootlets of growing 

 vegetation. We will send 

 >ou a copy of this Interest- 

 ing and instructive book free. 

 Write to-day. 

 NATURAL GUANO CO. 

 0«pt Xti, Aurora. 111. 



Mention The Review when 70a write. 



IMPROVED RETURN TUBULAR 

 - FIREBOX BOILER 



Johnston Heating: Co. 



131 B. 26th St., New York City 



...YOU... 



Wm Find ALL the BEST OFFERS 

 ALL the Time In the REVIEWS 

 CLASSIFIED ADVS. 



CHRISTMAS 

 PRESENT 



GET ONE FOR YOUR BOILER 



^i 



EQUAL TO STEAM 



5 



Your system of piping, together with your 

 improved greenhouse Generator, is an imp ove- 

 ment over steam in many way* We were on the 

 marliet to buy high prrssure steam, but after 

 receiving such reports of your improved hot water 

 system we concluded that your experirnce was 

 worth something, and we have been delighted at 

 the result, and so glad we put in the Generator 

 Hot Water System, instead of steam. 



W. J. MILLER & SON, Pontiac, lU. 



THE KROESCHELL GENERATOR 



THE HIQH SPEED GEAR 

 FOR HOT WATER HEATING 



444 W. Erie St., CHICAQO, ILL. 



Mention The Review when you write. 



Write for Catalotrne. 



Tree Tibi uA Bran Bmp 



Jtrdiiieiti. 



The extension stave foot 

 prevents the bottom from 

 rotting. No chance for water 

 to collect. 



The tawricM WM4Mvan Mf|. 

 Ce. 



Toledo, Ohio. U. S. A. 



Mention The Keview when you write. 



