July 4, 1912. 



The Florists' Review 



85 



ac 



-" "- 



3C 



ac 



ac 



ac 



fpLORISTS* FUEL DIRECTORY^ 



^1 ■ ■ —^ 



II IC 



ac 



CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB 



QUALITY PROMPT SHIPMENT PREPARATION 



c 

 c 



B 



C 



c 



B 

 C 



c 



C. C. B. POCAHONTAS SMOKELESS COAL 



The unqualified favorite of leading florists for twenty years. 



MAJESTIC 



A biocky splint coal. Intense, uniform and lasting heat. Minimum impurities, 

 a lower freight rate than Pocahontas. A trial car brings a permanent customer. 



Carries 



c CASTNER, CURRAN & BULLITT, Inc., 



PEOPLES QAS 

 BUILDING 



CHICAGO, ILL. 



B CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB CCB 



C 

 C 



B 



Mention The Review when yon write. 



SMITH, LINEAWEAVER& CO. 



COAL 



Anttarftcite, Bitaminons, Coke and Gm Coal 



T^IIrBuTfii:.,. Philadelphia 



jftrotton Th6 ItoTlew when yon wiif . 



furnace is not large enough. The 

 plumber who put in the heating plant 

 said it would heat the dwelling, the 

 present greenhouse and another one. We 

 need more space under glass and should 

 like to know whether our heating plant 

 will stand it. Last fall, when we first 

 built the fires, we tried to heat the resi- 

 dence, but got the greenhouse too warm 

 and made the carnation stents weak. 

 We can shut the heat away from any 

 or all of the benches, but not out of the 

 overhead pipes in the greenhouse. The 

 Ijottom of the expansion tank is nine 

 feet six inches above the greenhouse 

 iloor. V. A. A. 



Nothing is said regarding the size of 

 the dwelling house, but it is an 8-room 

 house and it would be a small room 

 which would not need more than twenty- 

 eight square feet of radiation, which is 

 the amount said to be used for the entire 

 residence. The greenhouse would prob- 

 ably require about 400 square feet of 

 radiating surface and the dwelling house 

 from 200 to 300 feet more, according to 

 the size of the rooms to be heated. I 

 am not sure regarding the size of the 

 heater mentioned, but from the fore- 

 going figures it should be possible to 

 determine whether or not it will heat an 

 additional house. 



SLOW CIRCULATION. 



I wish to ask you about my heating 

 plant. My houses are heated by hot 

 "water. The expansion tank is five feet 

 above the pipes. The water moves much 

 too slowly in the pipes and I should like 

 to know whether the trouble could be 

 remedied by putting in a generator. 

 Would a cast-iron boiler stand a gen- 

 erator? The plumber in this place says 

 a generator would save one-third of the 

 fuel. W. S. L. 



There is nothing in the foregoing in- 

 quiry which gives any idea of the cause 

 of the trouble. If the expansion tank 

 is elevated five feet, it is all that is 



Save Labor and Expense 



=^By the use of^^^^^^^= 



BERWIND SMOKELESS COAL 



^^^^=^^^=^^^^==:^= from ^^=^^ 



Pocahontas and New River 



Mines of 



BERWIND-WHITE COAL MINING CO. 



Office: 1805 Peoples Qas Building, CHICAQO 



Telephone Randolph 3901 



aieuuoo iDe Keview wnen you wnie 



R. C. WHITSETT COAL S MINING CO. 



Phone Harrison 8032 610 So. Dearborn St., CHIOACK) 



We IMake a Specialty of Supplying tiie Florists' Trade. 



MINERS AND SHIPPERS £>^ £\ M V 

 of the FOLLOWING GRADES of \^ \3 A% L 



SUNSHIilE 



INDIANA BRAZIL BLOCK 



POCAHONTAS 



WCSr VIRGINIA SPUNT 



YOUGHIOGHENY and 

 SOUTNCRN ILLINOIS 



Write us for names of satisfied customers, both as to quality and senice, who have used 

 our coal for the past five to ten years. 



Write for our prices before placing your contract. 



Mention The Rpvlew when you write. 



POCAHONTAS COAL SALES CO 



MAIN OFFICE. CINCINNATI, OHIO. 



1207 Fisher 

 Phones: Harrison 



PRODUCERS OF 



Genuine No. 3 Thick Vein 



^^SSSi CHICAGO, ILL. 



Pocahontas Smolceiess 

 Glen Alum Splint 

 Standard Thacker Splint 



COAL 



Mlnos 

 on N. & W. Ry. 



( Pocahontas, 3000 tons daily. 

 Capacity : < Olen Alum Splint. 3C00 tons daily. 



( Standard Thacker Splint. 3000 tons daily. 



Mention The Review when you write. 



necessary, provided the system is prop- 

 erly arranged. If the return pipes are 

 above the top of the heater and all of 

 the pipes are carried with a slight fall, 

 a good circulation should be obtained. 



The use of a generator will improve the 

 circulation of the water. This often re- 

 sults not only in a considerable saving 

 of fuel, but makes it possible to secure 

 a much higher temperature, as by the 



