eS =. 
CONVICT ROAD CAMP, FULTON COUNTY, GEORGIA. 21 
Gai tae lan ty lac ketene mes te tee Ses BF PSS ERAN SEA, RE Oe I Es eas) lla $0. 60 
Gpletbyasinieh placleitedss 2ee SL ee Se 20s EN Es LU 30) S20 PX . 66 
Baleryed nen, plagk reducins iellsysstas 4 ork) Seo e hie Hess Pease Laced ee . 20 
Peli ineh: black teducmovellsaary fro05 seer Sk a a Sa aks .18 
4 1-inch black ells.-...--- SR REA een See en ee Spee nee ee . 30 
% TiSetetceiay lleva Spal | 0a ay oS epee ain | eae aed ane OF, sr aa el len i ieee aa . 84 
PelomehvnlackiG xd, tinionses* seas. Godse: Ba. de Bigs ae Soy Late ents . 60 
6z-imeh black Ge unions: ? 423.653.228.302.) epee See a. os 1.08 
Bae uae GIS ULCLG (CLIN tien ste ee meet Stee EO A Pe) Sara ee Ne m7, 
Bee ine nmiose Pius este. Soe. 2 ak Ce vey, JR ee hg Ey 4. 50 
Second-hand piping: 
30 feet 2-inch galvanized pipe 
45 feet $-inch galvanized re fe ee See a oe ONES ie ne ae ae 11. 65 
65 feet 1-inch galvanized pipe 
PRUE MLCT NACA LOLS ean to clic Pac nte See eee ee a we a Wr ee Sy 17. 00 
Pte reMlOnnOL- water tales: 27) 2ch2) Jt SES oe EI er kee ce oa 8.75 
oialcost water-supply equipment... J. --Jse Sete acei-est- ase eee 452. 61 
Once each day, except bathing days, the engine was operated from 
a half hour to one hour to charge the air tank with air at 100 pounds 
pressure. On bathing days it was necessary to recharge the tank 
immediately before the bathing began. With the tank charged a 
supply of water was always available at any of the faucets, as the 
opening of a faucet automatically set the pump to work. 
Four shower fixtures were provided in the bath tent, and water was 
heated for bathing by two heaters coupled in tandem, having a com- 
bined water-heating surface of 880 square inches, and a grate area 
of 127 square inches. A 40-gallon tank was installed for the storage 
of hot water. 
Table 7 shows the results of a test of the efficiency of the hot-water 
_ system. 
TABLE 7.—Results of a test of the hot-water system at the Fulton County, Ga., Experi- 
- mental Convict Camp. 
Heater dimensions: 
SURES AIG Os aa a ee ee eee emer 23 127 square inches. 
22 Sel IVE} CLS ag gh a IE Dll ep a 880 square inches. 
Temperatures: 
Besa wciiets: PSE 1 a8 a8) 2152.05 ee ee: 57° F. 
IBLE Wey Some Cie ae oe rr es er oh peepee eye nes 105° F. 
PUIG io A i Me NB 94° F. 
PAOUMMLOORS says pice que ce ee cig hc)a = aus Ae e ooo gate eee Das se 46° F, 
Time: 
MEISE ARLCCE ee: Shes MAE SALE ee TSS OR Se 3.30 p. m. 
Bathing started? (94.22. Jose! fh: pes Ly Bae 5.00 p. m. 
Bapathp tosh eGs. ech) hn oc pee rhs. myer eoeeyene 0 bbs 5.30 p. m. 
Fuel consumption: 
“GCS! ; {SERS Be Fee I, 8 ete ane ee eae RMR TP PRG eae 5 pounds. 
Cae ate ee ee oe ae ean e ue goer ese ees 32 pounds. 
Water consumption (metered), 80 cubic feet. ......-.--2-------- 600 gallons. 
Hot water remaining in tank at 5.30 p. m...-....-----.2..------ 20 gallons. 
Nianaper oi immates bathedens 222 25:2) ecld-ed---- seb sees 40 
