xin, A, 3 Ycasiano and Valencia: Producer-gas Plant 

 Table IV. — Results of tests of entire power plant. 



117 



Test 

 No. 



Dura- 

 tion. 



Fuel. 



Total. 



Coal con- 

 sumed. 



Power 

 gen- 

 erated. 



Power 

 con- 

 sumed 

 by auxi- 

 liary ma- 

 chinery. 



Net 

 power 

 gener- 

 ated. 



Water 

 used in 

 genera- 

 tor and 

 for clean- 

 ing the 

 gases. 



Water 

 for cool- 

 ing the 

 engine. 



1 



2 



3 



4 



5 



6 



7 



8 



9 



10 



11 



12 



13 



14 



15 



16 



17 



18 



19 



20 



Hrs. 

 6 

 8 



6.25 

 8 

 8 

 6 

 8 

 8 

 8 

 6 

 8 

 8 

 8 



7 

 49.5 



7 



8 



8 

 56.0 





Kilos. 

 296 

 317 

 328 

 396 

 396 

 242 

 391 

 389 

 416 

 323 

 400 

 380 

 428 

 417 

 301 



2.321 

 210 

 222 

 220 



1,955 



k. w. h. 



205 



278 



238 



298 



320.8 



210 



312 



301 



303 



233 



320 



287 



250 



275 



236 

 1,607 



255 



270 



236 

 1,816 



k. w. h. 

 32.60 

 36.40 

 29.37 

 40.10 

 39.44 

 24.45 

 41.28 

 37.60 

 39.20 

 28.32 

 39.44 

 39.76 

 36.10 

 39.85 

 42.91 



275. 73 

 35.50 

 44.80 

 39.60 



291. 06 



k. w. h. 

 172.40 

 241.60 

 208.63 

 257. 90 

 281.36 



185. 55 

 270. 72 

 263. 40 

 263.80 

 204.68 



280. 56 

 247. 24 

 213.90 

 235. 15 

 194.09 



1,331.27 

 219. 50 

 225.20 

 196. 40 



1, 524. 94 



CM. m. 

 16.70 

 15.28 

 13.50 

 18.00 

 10.90 

 6.00 

 11.40 

 13.25 

 11.70 

 9.50 

 10.90 

 11.10 

 11.00 

 11.80 

 17.70 

 75.93 

 16.60 

 16.40 

 20.80 

 83.05 



cu. m. 

 23.30 

 25.80 

 20.25 

 28.05 

 27.10 

 16.40 

 26.70 

 25.35 

 28.90 

 20.50 

 31.50 

 32.80 

 34.10 

 32.00 

 31.10 



166. 70 

 28.40 

 32.50 

 34.70 



250.20 



do 



do.. 



do 



do _ 



do 



do-- 



do 



do 



do 



do 



.. do 



-do -. 



- do --. - 



.. do 



do... 





do.. 



do 



do- -.. 



