118 The Philippine Journal of Science 



Table IV. — Results of tests of entire power plant — Continued. 



Test 

 No. 



Fuel. 



Hourly quantities. 



Coal con- 

 sumed. 



Power 

 gen- 

 erated. 



Power 



con- 

 sumed 

 by auxi- 

 liary ma- 

 chinery. 



Net 

 power 

 gener- 

 ated. 



Water 

 used in 

 genera- 

 tor and 

 for clean- 

 ing the 



gases. 



1 



Water 

 for cool- 

 ing the 

 engine. 



, 1 

 2 

 8 



4 

 5 

 6 



7 



9 



10 

 11 



. 12 

 13 



< 14 



! 16 

 17 

 18 

 19 

 20 





Kilos. 

 49.33 



k. w. h. 

 34.16 

 34.75 

 38.08 

 37.25 

 40.10 

 42.00 

 39.00 

 37.62 

 37.87 

 38.83 

 40.00 

 35.87 

 31.25 

 34.37 

 33.71 

 32.46 

 36.43 

 33.75 

 29.50 

 33.01 



k. w. h. 

 5.43 

 4.55 

 4.69 

 5.01 

 4.93 

 4.89 

 5.16 

 4.70 

 4.90 

 4.72 

 4.93 

 4.97 

 4.51 

 4.98 

 6.13 

 5.57 

 5.07 

 5.60 

 4.95 

 5.29 



k. w. h. 

 28.73 

 30.20 

 33.38 

 32.23 

 35.17 

 37.11 

 33.84 

 32.92 

 32.97 

 34.11 

 35.07 

 30.90 

 26.73 

 30.39 

 27.58 

 26. 89 

 31.36 

 28.15 

 24.55 

 27.72 



cu. in. 

 2.783 

 1.910 

 2.160 

 2.250 

 1.362 

 1.200 

 1.426 

 1.656 

 1.462 

 1.585 

 1.362 

 1.387 

 1.375 

 1.475 

 2.528 

 1. 533 

 2.371 

 2.050 

 2.600 

 1.510 



cu. in. 

 3.883 

 3.225 

 3.240 

 3.506 

 3.387 

 3.280 

 3.337 

 3.165 

 3.612 

 3.416 

 3.937 

 4.100 

 4.262 

 4.000 

 4.442 

 3.367 

 4.057 

 4.062 

 4.337 

 4.549 



do 



do.-_. 



do._ 



do 



do 



do 



do 



do 



do.... 



do 



do - 



do 



do - 



do - 



do .- 



39.62 

 52.48 

 49.50 

 49.50 

 48.40 

 48.87 

 48.62 

 52.00 

 53.93 

 50.00 

 47.50 

 53.50 

 52.12 

 43.00 

 46.88 

 30.00 

 27.75 

 27.50 

 35.54 





do 1 



do--- . - -. 



do 





