XIII, A, 6 Ycasiano: Data on Steairning Tests of Coals 



343 



From Table II, page SIS. 



Test 

 No. 



Equivalent in kilos 

 from and at 100° C. 



Factor of evaporation. 



Horse powe 



•developed. 



Percentage of 



builders' hoTse povf er 



developed. 





















Former 

 value. 



Recalcula- 

 ted value. 



Former 

 value. 



Recalcula- 

 ted value. 



Former 

 value. 



Recalcula- 

 ted value. 



Former 

 value. 



Recalcula- 

 ted value. 



1 



10.538 



9.666 



1. 1769 



1. 0786 



96.2 



88.2 



128 



117 



2 



10. 432 



9.566 



1.1754 



1. 0779 



95.2 



87.3 



127 



116 



3 



• 9.453 



8.802 



1. 1750 



1. 0941 



86.3 



80.3 



115 



107 



4 



7.862 



7.336 



1. 1734 



1.0950 



83.7 



78.1 



112 



104 



5 



8.579 



7.989 



1. 1724 



1. 0918 



81.2 



75.5 



108 



100.6 



6 



8.066 



7.458 



1. 1769 



1.0898 



73.5 



68.0 



98 



91 



7 



7.169 



6.703 



1. 1749 



1.0986 



91.6 



86.6 



122 



120 



8 



9.734 



8.984 



1. 1742 



1.0838 



88.8 



82.0 



118 



109 



9 



9.505 



8.769 



1. 1767 



1.0848 



91.1 



83.9 



121 112 



10 



9.058 



8. 309 



1. 1773 



1.0809 



77.1 



70.8 



103 94 



11 



6.863 



6.311 



1. 1749 



1.0820 



61.8 



56.9 



82 



76 



12 



6.994 



6.441 



1. 1749 



1.0820 



63.8 



88.7 



85 



78 



13 



10.064 



9.399 



1.1746 



1. 0971 



91.8 



85.8 



122 



114 



14 



9.384 



8.740 



1. 1752 



1. 0948 



88.2 



81.1 



117 



108 



15 



5.019 



4.624 



1. 1642 



1.0730 



80.2 



73.8 



107 



98 



16 



10.802 



9.505 



1. 1757 



1.0848 



94.0 



86.7 



126 



115 



17 



7.847 



6.721 



1. 1780 



1.0778 



85.3 



78.0 



114 



104 



18 



9.041 



8.214 



1.1785 



1.0708 



77.0 



69.9 



103 1 93 





From Table II, 



page 316. 





Test 

 No. 



Equivalent evaporation of water from and 

 at 100° C. per hour. 



Kilos. 



1 



Per square decimeter of 

 water-heating surface. 



Former 

 value. 



Recalculated 

 value. 



Former 

 value. 



Recalculated 

 value. 



1 



1, 505. 4 



1, 380. 8 



0.232 



0.190 



2 



1, 490. 3 



1,366.5 



0.230 



0.188 



3 



1,350.4 



1,257.4 



0.209 



0.173 



4 



1,310.3 



1.222.6 



0.203 



0.169 



5 



1,271.0 



1,183.5 



0.197 



0.163 



6 



1,150.7 



1,065.4 



0.178 



0.147 



7 



1,433.8 



1,340.6 



0.222 



0.185 



8 



1, 390. 6 



1, 283. 4 



0.216 



0.177 



9 



1, 425. 7 



1,315.4 



0.220 



0.181 



10 



1,207.7 



1, 107. 8 



0.187 



0.153 



11 



967.5 



891.0 



0.150 



0.123 



12 



999.1 



920.1 



5.154 



0.127 



13 



1, 437. 7 



1,342.7 



0.222 



0.171 



14 



1,373.3 



1,279.2 



0.213 



0.176 



15 



1, 254. 7 



1,156.0 



0.194 



0.159 



16 



1,471.7 



1,357.0 



0.227 



0.187 



17 



1,335.8 



1,222.0 



0.207 



0.168 



18 



1,205.5 



1,095.2 



0.187 



0.151 



