Volume II - 66 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 05 
Description 
Supply 
Supply Discharge 
Supply Discharge 
Exhaust 
Exhaust 
Exhaust 
Configuration 
Temperature (°C) 
RH 
Configuration 
Temperature (°C) 
RH 
Slot 
18.8 
61% 
High 
22 
50% 
Change 
Rack 
Rack 
Number of 
Total mass of 
Room 
Station 
Orientation 
Density 
Mice in Room 
Mice in Room 
Pressurisation 
ON 
On wall 
Single 
1050 
21000 gr 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
Cage Occupied Zone 
Analysis Results 
Temperature 
n 
p 
RH 
op 
(ppm) 
Mean 
212B 
72.10 
1742 
62.51% 
S.b. 
0.25 
0.45 
276 
2.09% 
Max. 
22.86 
73.15 
2333 
67.21% 
Cage Occupied Zone NH3 (ppm) 
T5ay 
1 
2 
3 
4 
5 
5 
7 
10 
Mean 
0.91 
1.76 
2.72 
4.23 
6.32 
12.75 
16.66 
TT.31 
26.14 
Max. 
1.22 
2.36 
3.64 
5.67 
8.46 
12.03 
17.07 
22.30 
28.53 
34.99 
Room Breathing Zone 
