Volume II - Section III - Rankings of Results of Whole Room Runs 
Page II • 37 
3. RANKINGS OF RESULTS OF WHOLE ROOM RUNS 
3.1 Introduction 
The following tables present rankings of the results of the CFD room simulations based on Room 
(scientists’ breathing zone) and cages mean values for CO 2 and NH3 (day 4) concentrations, 
temperature, and relative humidity. The tables start with the case with the lowest value and list 
the rest in ascending order. The case number should be used to identify all details of the case. 
The supply diffuser type, exhaust location, supply flow rate, and supply discharge temperature 
are given to provide a quick overview of the case. 
Discussion of these tables can be found in volurpe I, section 3.3. 
