Volume II - Section I - Introduction 
Page n - 21 
Case Name 
Supply 
Diffuser T)rpe 
Exhaust 
Location and 
Number 
Change 
Station 
(Design/ 
Status) 
Rack 
orientation 
Rack density 
Pressure of 
Room to 
Corridor 
Supply 
Temperature 
°C (T) 
Supply ACH 
Case 43 
Lx)w Ind 
(rotated by 
90°) 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18,8 (6S.8) 
15 
Case 44 
Radial 
(rotated by 
90°) 
Ceiling (x2) 
Tboren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 45 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg, SOcfm 
18.8 (6S.8) 
15 
Case 46 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neutral 
18.8 (6S.8) 
15 
Case 47 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. SOcfm 
18.8 (6S.8) 
15 
Case 48 
Radial 
Ceiling (x2) 
Thoren/ ON 
(swapped with 
rackl ) 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 49 
Radial 
Ceiling (x2) 
Thoren/ ON 
(swapped with 
rack2) 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 50 
Radial 
Ceiling (x2) 
Thoren/ ON 
(swapped with 
rack3) 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 51 
Radial 
Ceiling (x2) 
Thoren/ ON 
(swapped with 
rack4) 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 52 
Radial 
Ceiling (x2) 
Thoren/ ON 
(swapped with 
racks) 
Parallel 
Single 
Neg, lOOcfm 
18.8 (6S.8) 
15 
Case 53 
Radial 
Ceiling (x2) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 54 
Slot 
Ceiling (x2) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 55 
Low Ind 
Ceiling (x2) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 56 
Radial 
High (x4) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 57 
Radial 
Low (x4) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 58 
Slot 
High (x4) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 59 
Slot 
Low (x4) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (6S.8) 
15 
Case 60 
Low Ind 
High (x4) 
Lab. Ihod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 61 
Low Ind 
Low (x4) 
Lab. Prod. / 
ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 62 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
6.6 (43.9) 
5 
Case 63 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
14.8(58.6) 
10 
Case 64 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
18.9 (66.0) 
20 
Case 65 
Low Ind 
Low (x4) 
Lab. Prod. / 
ON 
Perjjendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 66 
Low Ind 
Low (x4) 
Lab. Prod. / 
ON 
Perpendicular 
Double 
Neg. lOOcfm 
6.6 (43.9) 
5 
Case 67 
Low Ind 
Low (x4) 
Lab. Prod. / 
ON 
Perpendicular 
Double 
Neg. lOOcfm 
14.8(58.6) 
10 
Case 68 
Low Ind 
Low (x4) 
Lab. Prod. / 
ON 
Perpendicular 
Double 
Neg. lOOcfm 
18.9 (66.0) 
20 
Case 69 
Radial 
High (x4) 
/ Low (x4) 
(Mass flow 
split evenly 
amongst 
exhausts) 
Thoren/ ON 
Parallel 
Single 
Neg. l(X)cfm 
18.8(65.8) 
15 
