Volume II - 104 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 24 
Description 
Supply 
Supply Discharge 
Supply Discharge 
Exhaust 
Exhaust 
Exhaust 
Configuration 
Temperature (°C) 
RH 
Configuration 
Temperature (°C) 
RH 
Low Ind 
18.8 
61% 
Low 
22 
50% 
Change 
Raek 
Rack 
Number of 
Total mass of 
Room 
Station 
Orientation 
Density 
Mice in Room 
Mice in Room 
Pressurisation 
ON 
Perp 
Single 
1050 
21000 gr 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
Cage Occupied Zone 
Analysis Results 
Temf^rature 
—CO— 
RH 
^ —sp 
(ppm) 
Mean 
22.10 71.78 
81 
49,75% 
S.D. 
(Tts in 
47 
Max. 
TTtS 82.00 
W 
Room Breathing Zone NH3 (ppm) 
Day 
^71 
2 
3 
4 
6 
7 
8 
g— - 
Mean 
O 
b 
00 
0.13 
oTS 
0.26 
0.36 
0.49 
0.66 
OS 
1.15 
Max. 
0.22 
0.42 
0.67 
0.06 
1.35 
1.87 
2.56 
3.46 
430 
on 
