Volume II -126 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 35 
Description 
Supply 
Supply Discharge 
Supply Discharge 
Exhaust 
Exhaust 
Exhaust 
Configuration 
Temperature (°C) 
RH 
Configuration 
Temperature (°C) 
RH 
Slot 
17,5 
66% 
Ceiling 
22 
50% 
Change 
Rack 
Rack 
Number of 
Total mass of 
Room 
Station 
Orientation 
Density 
Mice in Room 
Mice in Room 
Pressurisation 
ON 
Perp 
Double 
2100 
42000 gr 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
Tage^ccupietT^onT 
Analysis Results 
Temf^rature 
CO, 
RH 
T ^ 
(ppm) 
Mean 
19.96 67.92 
122 
57.37% 
S.D. 
1.01 l.$2 
50 
Max. 
78.67 
201 
Room Breathing Zone NH3 (ppm) 
Day 
1 
2 
3 
5 
6 
7 
8 
Mean 
0.06 
(Til 
OTO 
01^ 
035 
032 
1.21 
1.52 
T35 
2.06 
Max. 
0.15 
0.20 
0.45 
0.81 
1.32 
1.05 
2.80 
150 
53T 
