Volume II -152 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 48 
Description 
Supply 
Configuration 
Radial 
Supply Discharge 
Temperature (°C) 
18.8 
Supply Discharge 
RH 
61% 
Exhaust 
Configuration 
Ceiling 
Exhaust Exhaust 
Temperature (°C) RH 
22 50% 
Change Rack Rack 
Station Orientation Density 
ON (swapped with radDn wall Single 
Number of 
Mice in Room 
1050 
Total mass of 
Mice in Room 
21000 gr 
Room 
Pressurisation 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
Tage^ccupIeTZon^ 
Analysis Results 
