Volume II -206 
Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 75 
Description 
Supply 
Configuration 
Radial 
Supply Discharge 
Temperature (°C) 
18.8 
Supply Discharge 
RH 
61 % 
Exhaust 
Configuration 
Ceiling/Low 50/50 
Exhaust 
Temperature (°C) 
22 
Exhaust 
RH 
50% 
Change 
Station 
ON alt design 
Rack 
Orientation 
On wall 
Rack 
Density 
Single 
Number of 
Mice in Room 
1050 
Total mass of 
Mice in Room 
21000 gr 
Room 
Pressurisation 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
TTag^Cccupie^TonT 
Analysis Results 
Temperature 
— UJT~ 
— RH — 
^ cp 
(ppm) 
Mean 
2 1 .09 69.96 
48 
52.74% 
S.b. 
(HI ^ 
22 
Max. 
22.37 72.26 
247 
Room Breathing Zone NH3 (ppm) 
Day 
I 
2 
3 
5 
6 
7 
g 
9 
10 
Mean 
0.03 
0.05 
0T)7 
(TTl 
— m — 
— OT“ 
0715 
0.57 
urn 
Max. 
0,1 3 
0.25 
0.30 
OTt 
— n5s~ 
1.57 
Tn 
193 
3.60 
