Volume II -240 
Design Handbook on Animal Research Facilities Using Static Microisolators 
Casename Case 92 
Description 
Supply 
Configuration 
Low Ind 
Supply Discharge 
Temperature (°C) 
18.8 
Supply Discharge Exhaust 
RH Configuration 
61% Ceiling 
Exhaust Exhaust 
Temperature (°C) RH 
22 50% 
Change 
Station 
ON 
Rack 
Rack 
Number of 
Total mass of 
Room 
Orientation 
Density 
Mice in Room 
Mice in Room 
Pressurisation 
Perp all 5 on 1 wall 
Single 
1050 
21000 gr 
neg lOOcfm 
Room 
ACH 
15 
Cage 
Condition 
Top On 
Cage Occupied Zone 
Analysis Results 
