Page II - 8 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Figure 2.05 Alternative Change Station Design 
Modeling Assumptions 
@ Solar load was not modeled through the walls of the room. 
® The floor, ceiling, and walls were assumed to have no heat transfer, i.e., the surrounding 
areas were assumed to be at the same temperatures. 
® All surfaces were treated as smooth when calculating surface friction. 
