Volume I - Section II - Animal Room Variations 
Page II - 21 
Table 2.01 List of All Whole Room Runs 
Case Name 
Supply 
Diffuser Type 
Exhaust 
Location and 
Number 
Change 
Station 
(Design/ 
Status) 
Rack 
orientation 
Rack density 
Pressure of 
Room to 
Corridor 
Supply 
Temperature 
°C(°F) 
Supply ACH 
Basecase 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 02 
Radial 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 03 
Radial 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 04 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 05 
Slot 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 06 
Slot 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 07 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 08 
Low Ind 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 09 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 10 
Radial 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 11 
Radial 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
■ Case 12 
Slot 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 13 
Slot 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 14 ! 
Low Ind 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 15 
Low Ind 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 16 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 17 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 18 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 19 
Radial 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 20 
Slot 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 21 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 22 
Radial 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 23 
Slot 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 24 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 25 * 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 26 * 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 27 * 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
! Case 28 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
16.8(62.2) 
10 
Case 29 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
11.0 (51.8) 
5 
Case 30 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
19.8 (67.6) 
20 
Case 31 
Radial 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 32 
Slot 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 33 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 34 
Radial 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5(63.5) 
15 
Case 35 
Slot 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 36 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 37 
Radial 
Ceiling (x 1 ) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 38 
Slot 
Ceiling (xl) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 39 
Low Ind 
Ceiling (xl) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
