Page III - 2 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Table 3.01 List of All Whole Room Runs 
Case Name 
Supply 
Diff user Type 
Exhaust 
Location and 
Number 
Change 
Station 
(Design/ 
Status) 
Rack 
Orientation 
Rack Density 
Pressure of 
Room to 
Corridor 
Supply 
Temperature 
“CCD 
Supply ACH 
Base case 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg.. lOOcfm 
18.8(65.8) 
15 
Case 02 
Radial 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg.. lOOcfm 
18.8(65.8) 
15 
Case 03 
Radial 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case ©4 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 05 
Slot 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 06 
Slot 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 07 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 08 
Low Ind 
High (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 09 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 10 
Radial 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 11 
Radial 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 12 
Slot 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 13 
Slot 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 14 
Low Ind 
Ceiling (x2) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 15 
Low Ind 
Low (x4) 
Thoren/ OFF 
Parallel 
Single 
Neg. lOOcfm 
20.7 (69.3) 
15 
Case 16 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 17 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 18 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Pos. lOOcfm 
18.8(65.8) 
15 
Case 19 
Radial 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 20 
Slot 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 21 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 22 
Radial 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 23 
Slot 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 24 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 25 * 
Radial 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 26* 
Slot 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 27 * 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (65.8) 
15 
Case 28 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
16.8 (62.2) 
10 
Case 29 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
11.0 (51.8) 
5 
Case 30 
Low Ind 
Low (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
19.8 (67.6) 
20 
Case 31 
Radial 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 32 
Slot 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 33 
Low Ind 
Low (x4) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5(63.5) 
15 
Case 34 
Radial 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 35 
Slot 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 36 
Low Ind 
Ceiling (x2) 
Thoren/ ON 
Perpendicular 
Double 
Neg. lOOcfm 
17.5 (63.5) 
15 
Case 37 
Radial 
Ceiling (xl) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (65.8) 
15 
Case 38 
Slot 
Ceiling (xl) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8 (65.8) 
15 ; 
Case 39 
Low ind 
Ceiling (xl) 
/ Low (x4) 
(Mass flow in 
50/50 split) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
Case 40 
Radial 
Ceiling (x4) 
Thoren/ ON 
Parallel 
Single 
Neg. lOOcfm 
18.8(65.8) 
15 
