Volume I - Section IV - Experimental Work and Verification of CFD Methodology 
Page IV ~ 5 
2m (1.11”). Only one tunnel velocity, 30 fpm (0.15 m/s) was considered for each orientation. 
Instrumentation was included in one cage only. The other cage was left basically empty. 
These sets are summarized in table 4.1.01 below: 
Table 4.1.01 Table of Cage Condition Experimental Series 
Series Set 
Tracer 
Gas 
Injection 
Rate 
(L/ min) 
Sampling 
Method 
Mouse 
Heater 
Type 
Cage 
Orientation 
Tunnel 
Air 
Velocity 
Range 
tfpm) 
Base 
co 2 
1.0 
Steady 
DMH 
(On/ Off) 
Par, Perp, 
Vert 
15-100 
One 
co 2 
0.1 
Steady 
DMH 
(On only) 
Par, Perp 
15-50 
Two 
sf 6 
0.1 
Steady 
DMH 
(On only) 
Par, Perp 
15-50 
Three 
co 2 
0.1 
Steady 
DMH 
(On / Off) 
Par, Perp, 
Vert 
20, 40 
Four 
co 2 
0.1 
Steady 
SMO 
(On only) 
Par, Perp, 
Vert 
20, 30, 40 
Five 
co 2 
0.1 
Decay 
SMO 
(On only) 
Par, Perp, 
Vert 
20, 30, 40 
Six 
co 2 
0.1 
Steady 
DMH (On / 
Off); SMO 
(On Only) 
Par, Perp 
20,40 
Seven 
co 2 
0.1 
Steady 
DMH (On/ 
Off); SMO 
(On Only) 
Par, Perp 
20, 40 
Eight 
co 2 
0.1 
Steady 
SMO (On 
Only) 
Par, Perp 
30 
4. 1.1. 4 Experimental Procedure 
4. 1 . 1 .4. 1 Common Calibration Procedures 
The following calibration procedures were performed before all experimental test series. 
