age Ventilation Rate (c 
Page IV - 36 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Cage Ventilation Rate vs. Approach Velocity 
Series Set Six: C02@ 0.1 L /Min Injection Rate 
Sealed Cage Lips. Mouse Heater Type: DMH /SMO 
<y 0.04 
Approach Velocity (fpm) 
Para Cage Orientation: Heater On (DM H) 
Para Cage Orientation: Heater On (SM O) 
Perp. Cage Orientation: Heater On (DM H) 
Perp. Cage Orientation: Heater Off (DM H) 
— i — Para Cage Orientation: Heater Off (DM H) 
— ra— Perp. Cage Orientation: Heater On (SM O) 
Figure 4.29 Cage Ventilation Rate vs. Approach Velocity. Series Set Six. 
Cage Ventilation Rate vs. Approach Velocity 
Series Set Seven: C02 @ 0.1 L / Min Injection Rate 
Top. Mouse Heater Type: DMH /SMO 
Approach Velocity (fpm) 
■■■■♦ Para Cage Orientation; Heater On (DM H) 
Para. Cage Orientation: Heater Off (DM H) 
-||g- Perp. Cage Orientation; Heater On (SM O) 
Para Cage Orientation; Heater On (SM O) 
Perp. Cage Orientation; Heater On (DM H) 
Perp. Cage Orientation; Heater Off (DMH) 
Figure 4.30 Cage Ventilation Rate vs. Approach Velocity. Series Set Seven. 
